内容

概要

前提条件

要件

使用するコンポーネント

トラブルシュート

CGR が 3G モジュールを認識できることを確認する

3G モジュールは認識されているが接続がない場合の確認

IP アドレス接続の確認

ping の確認

TAC サービス要求を開く場合に収集する情報

関連情報

概要

このドキュメントでは、CG-OS 搭載の Cisco Connected Grid ルータ（CGR）1000 シリーズ ルータの 3G モジュールをトラブルシューティングする手順について説明します。この記事では、問題、原因、および問題を解決するための修復手順についても説明します。

モデムの問題をトラブルシューティングする場合、最初の手順は、CGR がモジュールを認識できるかどうかを判別することです。このドキュメントでは、その判別に必要な手順とプロセスの進め方について説明します。

著者：Cisco TAC エンジニア、Sumedha Phatak および Abhishek Kumar

前提条件

要件

次の項目に関する知識があることが推奨されます。

- アクティブなデータ プランによる 3G モジュールと SIM カードを搭載した CGR 1000 シリーズ ルータへの CLI アクセス。

- ルータの物理的な場所での 3G ワイヤレス ネットワーク カバレッジ。

使用するコンポーネント

このドキュメントの情報は、次のソフトウェアとハードウェアのバージョンに基づいています。

- CGR 1000 シリーズ ルータ

- Cisco CG-OS ソフトウェア

このドキュメントの情報は、特定のラボ環境にあるデバイスに基づいて作成されました。このドキュメントで使用するすべてのデバイスは、初期（デフォルト）設定の状態から起動しています。対象のネットワークが実稼働中である場合には、どのようなコマンドについても、その潜在的な影響について確実に理解しておく必要があります。

トラブルシュート

モデムの問題をトラブルシューティングする場合、最初の手順は、CGR がモジュールを認識できるかどうかを判別することです。

CGR が 3G モジュールを認識できることを確認する

3G モジュールを取り付けて設定した後で、CGR がモジュールを認識できないことがあります。

1. show cellular 3/1 allコマンドを実行して、CGRがモジュールを認識し、すべての関連情報を表示できるかどうかを確認します。出力のすべてのフィールドに「unknown」と表示される場合は、モジュールをリロードしてから最大 2 分間待ってからもう一度検証してください。

2.リロード後でも、すべてのフィールドに「unknown」と表示される場合は、セルラーインターフェイスをshut/no shutし、最大2分間待ってからshow cellular 3/1 allコマンドを再度実行します。

注：すべてのフィールド値に引き続き「unknown」と表示される場合は、Cisco TAC に連絡してモジュールの交換を依頼してください。上記のトラブルシューティングとシリアル番号情報が記載されている「show inventory」の出力を含むログを添付してください。

3G モジュールのリロード

次のコマンドを使用して 3G モジュールだけをリロードします。

ast03-cgr1120-cgosB# reload module 3

reloading module 3 ...

セルラー インターフェイスのバウンス

次のコマンドを使用して、セルラー インターフェイスの shut/no shut を行います。

ast03-cgr1120-cgosB# conf t

Enter configuration commands, one per line.  End with CNTL/Z.

ast03-cgr1120-cgosB(config)# interface cellular 3/1

ast03-cgr1120-cgosB(config-if)# shut   <<<<<<<<<<<<<<<<<   Wait for 30 sec

ast03-cgr1120-cgosB(config-if)# no shut

3G モジュールが起動して動作しているときの出力例

モジュールが動作しているときの「show cellular 3/1 all」の出力。

ast03-cgr1120-cgosB# sh cellular 3/1 all

Hardware Information

====================

Modem Firmware Version = T1_0_3_2AP R361 CNSZXD00000061 2011/04/15 17:40:48

Modem Firmware Built = 04/15/11

Modem Hardware Version = 1.0

International Mobile Subscriber Identity (IMSI) = 867941410

International Mobile Equipment Identity (IMEI) = 357115040246303

Factory Serial Number (FSN) = CC3159202581007 04/15/11

Modem status = Online

Current Modem Temperature = 35 deg C

Current Temperature State = Normal

Profile Information

===================

--- Profile 1 details ---

Status = Activated

Default: Yes

PDP Type: IPv4

Profile IP: 192.0.2.1

Profile APN: broadband

Authentication: None

Profile UserName:

Profile Password:

Data Connection Information

===========================

Data Transmitted = 460 bytes

Data Received = 420 bytes

Profile 1, Packet Session Status = ACTIVATED

IP Address = 192.0.2.1

Network Information

===================

Modem status = Online

Service status = Normal

Service type = Combined

Current Roaming Status = Home

Country Initials = USA

Network name = AT&T

Mobile Country Code (MCC) = 310

Mobile Network Code (MNC) = 410

Location Area Code (LAC) = 28986

Routing Area Code (RAC) = 1

Cell ID = 50434

Primary Scrambling Code = 2

PLMN Selection = Automatic

Radio Information

=================

Current band = WCDMA_V_850

Radio power mode = On

Channel number = 4359

Band selected = Auto

Current RSSI = -92 dBm

Band Information

================

Number of bands:   5

Band 1: WCDMA: NA

Band 2: GSM PCS 850

Band 3: GSM ALL

Band 4: WCDMA ALL

Band 5: AUTO BAND

Current LED values

==================

WWAN: green

RSSI: amber

SIM Slot 0: off

SIM Slot 1: green

Service: green

GPS: off

3G モジュールは認識されているが接続がない場合の確認

セルラー インターフェイスの確認

show ip interface brief command コマンドを発行し、セルラー インターフェイスが IP を受信し、ステータスが UP であることを確認します。インターフェイスが IP を取得できなかった場合は、引き続きトラブルシューティングを行います。

ast03-cgr1120-cgosB# sh ip int b

IP Interface Status for VRF "default"(1)

Interface            IP Address      Interface Status

Cell3/1              192.0.2.1       protocol-up/link-up/admin-up

信号強度の確認

受信信号強度表示（RSSI）は、3G モジュールによって受信された信号の強度を示します。これは、show cellular 3/1 radio コマンドを使用して確認できます。

ast03-cgr1120-cgosB# sh cellular 3/1 radio

Current band = WCDMA_V_850

Radio power mode = On

Channel number = 4359

Band selected = Auto

Current RSSI = -92 dBm

RSSI 値：

1.信頼性の高い接続には、RSSIが–90以上である必要があります。-60 より大きい RSSI は、強い信号強度を示します。

2. RSSIが–100未満の場合、モジュールはネットワークに接続できません。この原因には次のものが考えられます。

- セルラー インターフェイスが管理上ダウンしている。セルラー インターフェイスの no shut を行い、RSSI 値が変わるかどうかを確認します。

- モジュールが低電力モードでスタックしている。セルラー インターフェイスの shut/no shut を行い、RSSI 値が変わるかどうかを確認します。no shut を発行する前に 30 秒待ってください。

- アンテナがない、または正しく接続されていない。

- その地域に 3G サービス対象時間がない。

3. RSSIが–60より大きい場合は、より多くのトラブルシューティングが必要です。デバッグを有効にして、問題をさらに分類します。

IP アドレス接続の確認

1.発信コールが開始され、show ip interface briefコマンドとshow cellular 3/1 allコマンドを使用してIPアドレスがモジュールで受信されているかどうかを確認します。これを確認するデバッグのサンプル出力を次に示します。

2009 Feb  5 22:57:51.479132 dialer: Dialer1 is in READY state

2009 Feb  5 22:57:52 ast03-cgr1120-cgosB %DIALER-5-DIALER_DIAL_OUT: Dialer1 dial out cellular3/1 successfully

2009 Feb  5 22:57:52.572770 dialer: Dialer1 dial out cellular3/1 successfully

2009 Feb  5 22:57:55 ast03-cgr1120-cgosB %CELLPM-5-CELLPM_CON_EST: Connection Established

2009 Feb  5 22:57:55.317420 cellpm: Get Ip from modem 192.0.2.1

2009 Feb  5 22:57:55.995243 cellpm: interface cellular 3/1 IP address 192.0.2.1

2.発信コールが行われてもIPアドレスが受信されない場合は、ログを収集して切断理由をshow logで確認します | noコマンドを発行し、TACケースに添付します。

3.発信コール要求がない場合は、Initialize Over the Air(IOTA)を実行して、接続が可能かどうかを確認します（CDMAモジュールのみ）。

cellular3/1 cdma activate otasp *22899

（i）IOTA 接続が成功した場合は、ハードウェアや設定の問題がないか確認します。

- show interface cellular 3/1

- show controllers cellular 3/1

- show tech

（ii）IOTA 接続に失敗した場合は、原因をログで確認して、次のコマンドを発行します。

- show log |いいえ

接続に成功した場合のデバッグのサンプル出力を次に示します。

2009 Feb  5 22:57:37 ast03-cgr1120-cgosB %DIALER-5-DIALER_MODEM_UP: Modem active

2009 Feb  5 22:57:37.758585 dialer: modem changes from DISABLE to ENABLE

2009 Feb  5 22:57:37.758652 dialer: CHAT SCRIPT CHAT profile 1

2009 Feb  5 22:57:37.758722 dialer: Dialer1 is in READY state

2009 Feb  5 22:57:37.758764 dialer: Dial out interface service is not ready yet

2009 Feb  5 22:57:37.762968 cellpm: Plmn Ready: 0

2009 Feb  5 22:57:37 ast03-cgr1120-cgosB %CELLPM-5-CELLPM_SIM_STATUS: SIM Status: SIM Okay

2009 Feb  5 22:57:37.763128 cellpm: SIM Status: SIM Okay

2009 Feb  5 22:57:37.763231 cellpm: Rec'd Modem Radio Power Enable

2009 Feb  5 22:57:37.763520 cellpm: Receive modem enabled notification

2009 Feb  5 22:57:37 ast03-cgr1120-cgosB %CELLPM-5-CELLPM_MODEM_UP: Modem enabled

2009 Feb  5 22:57:37.766192 dialer: Modem Enable on interface 29100000

2009 Feb  5 22:57:37.766257 dialer: Rec'd cellular3/1 modem ENABLE notification

2009 Feb  5 22:57:37.766303 dialer: current modem state is ENABLE

2009 Feb  5 22:57:39.485643 cellpm: Network Service Status: Emergency

2009 Feb  5 22:57:39.485697 cellpm: Network Service Type: Invalid Service

2009 Feb  5 22:57:39.485932 cellpm: Send MTS opcode 183321 to sap 776 if_index 29100000

2009 Feb  5 22:57:39.488392 dialer: Modem service is out for interface 29100000

2009 Feb  5 22:57:39.488686 cellpm: Service Type: 0

2009 Feb  5 22:57:39.488787 cellpm: Registration Indication:

2009 Feb  5 22:57:39 ast03-cgr1120-cgosB %CELLPM-5-CELLPM_NETWORK_NAME:

2009 Feb  5 22:57:39.488851 cellpm:

2009 Feb  5 22:57:41.360863 cellpm: Network Service Status: Emergency

2009 Feb  5 22:57:41.360928 cellpm: Network Service Type: Invalid Service

2009 Feb  5 22:57:41.361704 cellpm: Send MTS opcode 183321 to sap 776 if_index 29100000

2009 Feb  5 22:57:41.364084 cellpm: Service Type: 0

2009 Feb  5 22:57:41.364157 dialer: Modem service is out for interface 29100000

2009 Feb  5 22:57:41.364938 cellpm: Registration Indication:

2009 Feb  5 22:57:41.365040 cellpm:

2009 Feb  5 22:57:41.466717 cellpm: Network Service Status: Emergency

2009 Feb  5 22:57:41.466770 cellpm: Network Service Type: Invalid Service

2009 Feb  5 22:57:41.467005 cellpm: Send MTS opcode 183321 to sap 776 if_index 29100000

2009 Feb  5 22:57:41.469358 cellpm: Service Type: 0

2009 Feb  5 22:57:41.469444 dialer: Modem service is out for interface 29100000

2009 Feb  5 22:57:41.469478 cellpm: Registration Indication:

2009 Feb  5 22:57:41.469568 cellpm:

2009 Feb  5 22:57:41.469645 cellpm: Network Service Status: Normal

2009 Feb  5 22:57:41.469689 cellpm: Network Service Type: Combined

2009 Feb  5 22:57:41.469733 cellpm: Modem Status Normal notify dialer

2009 Feb  5 22:57:41.469929 cellpm: Send MTS opcode 183299 to sap 776 if_index 29100000

2009 Feb  5 22:57:41.472329 dialer: Modem Enable on interface 29100000

2009 Feb  5 22:57:41.472382 dialer: Rec'd cellular3/1 modem ENABLE notification

2009 Feb  5 22:57:41.472427 dialer: current modem state is ENABLE

2009 Feb  5 22:57:41.477311 cellpm: MTS_OPC_CELLPM_SERVICE_READY send at port 3

2009 Feb  5 22:57:41.477369 cellpm: Service Type: 6

2009 Feb  5 22:57:41.477405 dialer: Modem service is ready for interface 29100000

2009 Feb  5 22:57:41.477456 dialer: Rec'd cellular3/1 AT port 3

2009 Feb  5 22:57:41.477466 cellpm: Registration Indication:

2009 Feb  5 22:57:41.477504 cellpm:  Network Name: AT&T

2009 Feb  5 22:57:41.477512 dialer: timer start #0 if_index 29100000

2009 Feb  5 22:57:41 ast03-cgr1120-cgosB last message repeated 2 times

2009 Feb  5 22:57:41 ast03-cgr1120-cgosB %CELLPM-5-CELLPM_NETWORK_NAME:  AT&T

2009 Feb  5 22:57:41.477560 dialer: Create time for msg 0

2009 Feb  5 22:57:41.477589 cellpm:

2009 Feb  5 22:57:41.477601 dialer: dialer_timer_start start timer

2009 Feb  5 22:57:48.636548 cellpm: cellpm_timer_msg_handler 0xb610052c Message type is 0

2009 Feb  5 22:57:48.636609 cellpm: timer expired if_index 29100000

2009 Feb  5 22:57:48.637429 cellpm: The onboard temp is 30

2009 Feb  5 22:57:48.639603 cellpm: temperature timer start if_index 29100000

2009 Feb  5 22:57:48.639666 cellpm: Create time for msg 0

2009 Feb  5 22:57:48.639711 cellpm: cellpm_timer_start start timer

2009 Feb  5 22:57:48.655443 cellpm: Modem Status Online

2009 Feb  5 22:57:48.655495 cellpm: temp 30 low crit -26 norm -23 admin state 1

2009 Feb  5 22:57:51.479034 dialer: timer expired if_index 29100000

2009 Feb  5 22:57:51.479098 dialer: CHAT SCRIPT CHAT profile 1

2009 Feb  5 22:57:51.479132 dialer: Dialer1 is in READY state

2009 Feb  5 22:57:52.572492 dialer: timeout_val 60 dialer_retry_num 1

2009 Feb  5 22:57:52.572572 dialer: timer start #1 if_index 29100000

2009 Feb  5 22:57:52.572627 dialer: Create time for msg 0

2009 Feb  5 22:57:52.572673 dialer: dialer_timer_start start timer

2009 Feb  5 22:57:52 ast03-cgr1120-cgosB %DIALER-5-DIALER_DIAL_OUT: Dialer1 dial out cellular3/1 successfully

2009 Feb  5 22:57:52.572770 dialer: Dialer1 dial out cellular3/1 successfully

2009 Feb  5 22:57:52.573620 cellpm: Plmn Ready: 0

2009 Feb  5 22:57:54.497230 cellpm: Network Service Status: Normal

2009 Feb  5 22:57:54.497286 cellpm: Network Service Type: Combined

2009 Feb  5 22:57:54.497329 cellpm: Modem Status Normal notify dialer

2009 Feb  5 22:57:54.497553 cellpm: Send MTS opcode 183299 to sap 776 if_index 29100000

2009 Feb  5 22:57:54.497771 dialer: Modem Enable on interface 29100000

2009 Feb  5 22:57:54.497831 dialer: Rec'd cellular3/1 modem ENABLE notification

2009 Feb  5 22:57:54.497880 dialer: current modem state is ENABLE

2009 Feb  5 22:57:54.508855 dialer: Modem service is ready for interface 29100000

2009 Feb  5 22:57:54.508924 dialer: Rec'd cellular3/1 AT port 3

2009 Feb  5 22:57:54.508972 dialer: Dial out timer started already

2009 Feb  5 22:57:54.509194 cellpm: MTS_OPC_CELLPM_SERVICE_READY send at port 3

2009 Feb  5 22:57:54.509259 cellpm: Service Type: 6

2009 Feb  5 22:57:55 ast03-cgr1120-cgosB %CELLPM-5-CELLPM_GSM_SESSION_ACTIVE: GSM Profile 1 is activated

2009 Feb  5 22:57:55.295970 cellpm: GSM profile 1 is activated

2009 Feb  5 22:57:55.296018 cellpm: Activation Status:             1

2009 Feb  5 22:57:55.296062 cellpm: Negotiated QoS:                1

2009 Feb  5 22:57:55.296103 cellpm: Negotiated Precedence:         2

2009 Feb  5 22:57:55.296334 cellpm: Send MTS - PKT SESS ACTIVATED to dialer

2009 Feb  5 22:57:55.296695 dialer: Session activated. Dialer1 stop dialing

2009 Feb  5 22:57:55 ast03-cgr1120-cgosB %DIALER-5-DIALER_CON_EST: Connection Established

2009 Feb  5 22:57:55.297250 cellpm: Rec'd session active notification

2009 Feb  5 22:57:55 ast03-cgr1120-cgosB %CELLPM-5-CELLPM_CON_EST: Connection Established

2009 Feb  5 22:57:55.317420 cellpm: Get Ip from modem 192.0.2.1

2009 Feb  5 22:57:55 ast03-cgr1120-cgosB %URIB-4-ZERO_NEXTHOP:  urib [3445] (default-base) Client "static" added 0.0.0.0 next hop and interface Cellular3/1 is not point-to-point

2009 Feb  5 22:57:55 ast03-cgr1120-cgosB %VSHD-5-VSHD_SYSLOG_CONFIG_I: Configured from vty by root on vsh.28455

2009 Feb  5 22:57:55.995243 cellpm: interface cellular 3/1 IP address 192.0.2.1

2009 Feb  5 22:57:55.998937 cellpm: Send MTS opcode 229378 to sap 776 if_index 29100000

2009 Feb  5 22:57:56.006669 cellpm: Service Type: 6

2009 Feb  5 22:57:56 ast03-cgr1120-cgosB %CELLPM-5-CELLPM_STATE_CHANGE: Moving to State: Connected

2009 Feb  5 22:58:03.100719 cellpm: Network Service Status: Normal

2009 Feb  5 22:58:03.100788 cellpm: Network Service Type: Combined

2009 Feb  5 22:58:03.100835 cellpm: Modem Status Normal notify dialer

2009 Feb  5 22:58:03.101097 cellpm: Send MTS opcode 183299 to sap 776 if_index 29100000

2009 Feb  5 22:58:03.103525 cellpm: Service Type: 6

2009 Feb  5 22:58:03.103560 dialer: Modem Enable on interface 29100000

2009 Feb  5 22:58:03.103610 dialer: Rec'd cellular3/1 modem ENABLE notification

2009 Feb  5 22:58:03.103654 dialer: current modem state is ENABLE

2009 Feb  5 22:58:03.732185 cellpm: Service Type: 6

2009 Feb  5 22:58:38.918415 cellpm: Get Ip from modem 192.0.2.1

2009 Feb  5 22:58:38.969173 cellpm: Get Ip from modem 192.0.2.1

ping の確認

セルラー インターフェイスが IP を受信し、インターフェイスのステータスが UP の場合は、パブリック IP への ping が成功したことを確認します。ping が成功していない場合は、デフォルト ルートが正しく設定されていることを確認します。

ast03-cgr1120-cgosB# conf t

Enter configuration commands, one per line.  End with CNTL/Z.

ast03-cgr1120-cgosB(config)#ip route 0.0.0.0 0.0.0.0 Cellular3/1

ast03-cgr1120-cgosB# show ip route

0.0.0.0/0, ubest/mbest: 1/0

*via Cellular3/1, [1/0], 00:06:05, static

ast03-cgr1120-cgosB# ping 8.8.8.8

PING 8.8.8.8 (8.8.8.8): 56 data bytes

64 bytes from 8.8.8.8: icmp_seq=0 ttl=54 time=1786.39 ms

64 bytes from 8.8.8.8: icmp_seq=1 ttl=54 time=89.716 ms

64 bytes from 8.8.8.8: icmp_seq=2 ttl=54 time=89.699 ms

64 bytes from 8.8.8.8: icmp_seq=3 ttl=54 time=99.691 ms

64 bytes from 8.8.8.8: icmp_seq=4 ttl=54 time=119.689 ms

--- 8.8.8.8 ping statistics ---

5 packets transmitted, 5 packets received, 0.00% packet loss

round-trip min/avg/max = 89.699/437.037/1786.39 ms

TAC サービス要求を開く場合に収集する情報

TAC サービス要求を開く場合は、3G モデムの問題をトラブルシューティングするために、この情報をリクエストに添付してください。

- 関連ログで実行されたトラブルシューティングの詳細

- show tech

- show log |いいえ

- debug chat trace

- debug cellular trace

- debug dialer trace

関連情報

- http://www.cisco.com/c/en/us/td/docs/routers/connectedgrid/modules/3g/Cisco_Connected_Grid_3G_Module_Installation_and_Configuration_Guide.html

- テクニカル サポートとドキュメント – Cisco Systems