目錄

簡介

必要條件

需求

採用元件

慣例

背景資訊

配置支援CISCO-STACK-MIB的交換機中的狀態陷阱更改

配置支援CISCO-C2900-MIB的交換機中的狀態陷阱更改

相關資訊

簡介

除了本地電源之外，某些Cisco交換機還允許冗餘電源(RPS)。本文提供有關如何使用SNMP監控這些交換機中RPS狀態的資訊。

必要條件

需求

本文件沒有特定需求。

採用元件

本檔案中的資訊是根據以下硬體和軟體版本：

- 支援CISCO-STACK-MIB的軟體映像 — 所有Catalyst OS版本和IOS映像都支援。

- 支援CISCO-C2900-MIB的軟體映像 — 支援Cat2900XL和Cat3500XL系列交換機的所有軟體映像和IOS映像。

- RPS 300

- RPS 600

注意：本文檔的內容僅適用於交換機，不適用於任何路由器型號。

本文中的資訊是根據特定實驗室環境內的裝置所建立。文中使用到的所有裝置皆從已清除（預設）的組態來啟動。如果您的網路正在作用，請確保您已瞭解任何指令可能造成的影響。

慣例

如需文件慣例的詳細資訊，請參閱思科技術提示慣例。

背景資訊

RPS裝置當前未傳送任何陷阱或系統日誌消息，以通知狀態更改。但是，可以通過從連線RPS的交換機讀取以下MIB對象之一來跟蹤該狀態：

- 對於支援CISCO-STACK-MIB的交換器，對象為chassisPs2Status(1.3.6.1.4.1.9.5.1.2.7)

chassisPs2Status OBJECT-TYPE

SYNTAX        INTEGER {

other(1),       -- none of the following

ok(2),          -- status ok

minorFault(3),  -- minor problem

majorFault(4)   -- major problem

}

MAX-ACCESS    read-only

STATUS        current

DESCRIPTION   "Status of power supply number 2. If the status is

not ok, the value of chassisPs2TestResult gives

more detailed information about the power supply's

failure condition(s)."

::= { chassisGrp 7 }

- 對於支援CISCO-2900-MIB的交換機，對象為c2900InfoRedantPowerSupplyInfo(1.3.6.1.4.1.9.9.87.1.1.9)

c2900InfoRedunantPowerSupplyInfo OBJECT-TYPE

SYNTAX  INTEGER {

absent(1),

connectedFunctional(2),

connectedNotFunctional(3),

functionalPrimaryFailed(4)

}

MAX-ACCESS  read-only

STATUS current

DESCRIPTION

"The switch allows a redundant power supply in addition

to its local power supply. Only one power source can be

supplying power to a unit.

absent(1) :the redundant power supply is not connected

to the switch.

connectedFunctional(2) : the redundant power supply is

connected to the switch and operational.

connectedNotFunctional(3): the redundant power supply

is connected to the switch, but cannot supply

power to the system.

functionalPrimaryFailed(4): the redundant power supply

is installed, powered on, and operational,

but a failure exists in the local power

supply system."

::= { c2900SysInfo 9 }

使用RMON警報和事件組，您可以配置交換機，以便它向指定的管理站傳送SNMP陷阱格式的警報。

配置支援CISCO-STACK-MIB的交換機中的狀態陷阱更改

您應在支援CISCO-STACK-MIB的交換機中配置這些命令，以便在RPS的狀態從ok(2)更改為majorFault(4)時獲取RMON事件，該事件作為SNMP陷阱轉發到NMS工作站：

rmon event 65 trap public description "RPS is not ready" owner yourname

rmon event 66 trap public description "RPS is ready" owner yourname

rmon alarm 222 1.3.6.1.4.1.9.5.1.2.7.0 10

absolute rising-threshold 4 65 falling-threshold 2 66 owner yourname

配置支援CISCO-C2900-MIB的交換機中的狀態陷阱更改

您應在支援CISCO-C2900-MIB的交換機中配置這些命令，以便在RPS的狀態從connectedFunctional(2)變為absent(1)時獲取RMON事件，該事件將作為陷阱轉發到NMS工作站：

rmon event 67 trap public description "RPS not ready" owner yourname

rmon event 68 trap public description "RPS ready" owner yourname

rmon alarm 444 1.3.6.1.4.1.9.9.87.1.1.9.0 5

absolute rising-threshold 2 68 falling-threshold 1 67 owner yourname

相關資訊

- 從命令列介面(CLI)配置RMON警報和事件設定

- 技術支援 - Cisco Systems