目录

简介

先决条件

要求

使用的组件

规则

背景信息

在支持CISCO-STACK-MIB的交换机中配置状态陷阱的更改

在支持CISCO-C2900-MIB的交换机中配置状态陷阱的更改

相关信息

简介

除本地电源外，某些思科交换机还允许冗余电源(RPS)。本文档提供有关如何使用SNMP监控这些交换机中RPS的状态的信息。

先决条件

要求

本文档没有任何特定的要求。

使用的组件

本文档中的信息基于下列硬件和软件版本：

- 支持CISCO-STACK-MIB的软件映像 — 在所有Catalyst OS版本和IOS映像中均受支持。

- 支持CISCO-C2900-MIB的软件映像 — 在Cat2900XL和Cat3500XL系列交换机的所有软件映像中都支持，以及IOS映像。

- RPS 300

- RPS 600

注意：本文档的内容仅适用于交换机，不适用于任何路由器型号。

本文档中的信息都是基于特定实验室环境中的设备编写的。本文档中使用的所有设备最初均采用原始（默认）配置。如果您使用的是真实网络，请确保您已经了解所有命令的潜在影响。

规则

有关文件规则的更多信息请参见“ Cisco技术提示规则”。

背景信息

RPS设备当前未发送陷阱或系统日志消息，通知状态发生更改。但是，可以通过从连接RPS的交换机读取以下MIB对象之一来跟踪该状态：

- 对于支持CISCO-STACK-MIB的交换机，对象为chassisPs2Status(1.3.6.1.4.1.9.5.1.2.7)

chassisPs2Status OBJECT-TYPE

SYNTAX        INTEGER {

other(1),       -- none of the following

ok(2),          -- status ok

minorFault(3),  -- minor problem

majorFault(4)   -- major problem

}

MAX-ACCESS    read-only

STATUS        current

DESCRIPTION   "Status of power supply number 2. If the status is

not ok, the value of chassisPs2TestResult gives

more detailed information about the power supply's

failure condition(s)."

::= { chassisGrp 7 }

- 对于支持CISCO-2900-MIB的交换机，对象为c2900InfoRedunantPowerSupplyInfo(1.3.6.1.4.1.9.9.87.1.9)

c2900InfoRedunantPowerSupplyInfo OBJECT-TYPE

SYNTAX  INTEGER {

absent(1),

connectedFunctional(2),

connectedNotFunctional(3),

functionalPrimaryFailed(4)

}

MAX-ACCESS  read-only

STATUS current

DESCRIPTION

"The switch allows a redundant power supply in addition

to its local power supply. Only one power source can be

supplying power to a unit.

absent(1) :the redundant power supply is not connected

to the switch.

connectedFunctional(2) : the redundant power supply is

connected to the switch and operational.

connectedNotFunctional(3): the redundant power supply

is connected to the switch, but cannot supply

power to the system.

functionalPrimaryFailed(4): the redundant power supply

is installed, powered on, and operational,

but a failure exists in the local power

supply system."

::= { c2900SysInfo 9 }

使用RMON警报和事件组，可以配置交换机，使其以SNMP陷阱格式向指定的管理站发送警报。

在支持CISCO-STACK-MIB的交换机中配置状态陷阱的更改

当RPS状态从ok(2)更改为majorFault(4)时，您应在支持CISCO-STACK-MIB的交换机中配置以下命令，以获取RMON事件，并作为SNMP陷阱转发到NMS站：

rmon event 65 trap public description "RPS is not ready" owner yourname

rmon event 66 trap public description "RPS is ready" owner yourname

rmon alarm 222 1.3.6.1.4.1.9.5.1.2.7.0 10

absolute rising-threshold 4 65 falling-threshold 2 66 owner yourname

在支持CISCO-C2900-MIB的交换机中配置状态陷阱的更改

当RPS状态从connectedFunctional(2)更改为缺失(1)时，您应在支持CISCO-C2900-MIB的交换机中配置这些命令，以获得RMON事件，并作为陷阱转发到NMS站：

rmon event 67 trap public description "RPS not ready" owner yourname

rmon event 68 trap public description "RPS ready" owner yourname

rmon alarm 444 1.3.6.1.4.1.9.9.87.1.1.9.0 5

absolute rising-threshold 2 68 falling-threshold 1 67 owner yourname

相关信息

- 从命令行界面 (CLI) 配置 RMON 警告与事件设置

- 技术支持 - Cisco Systems