Inhoud

Inleiding

Voorwaarden

Vereisten

Gebruikte componenten

Conventies

Tractieprocedure

Gerelateerde informatie

Inleiding

Wanneer apparaten redundante voedingen bevatten, kunt u ervoor kiezen om het apparaat vallen te laten genereren wanneer een van de voedingen sterft of de toestand verandert. Splitsen bestaan op zowel routers als switches en zij melden een staatswijziging of -storing, en wijzen op verdere informatie over de aard van de verandering. Dit document legt uit hoe u kunt opsporen wanneer een van de redundante voedingen verdwijnt of de status wijzigt door gebruik te maken van Simple Network Management Protocol (SNMP).

Voorwaarden

Vereisten

Er zijn geen specifieke vereisten van toepassing op dit document.

Gebruikte componenten

De informatie in dit document is geldig voor Cisco-routers en switches die redundante voedingen hebben.

De informatie in dit document is gebaseerd op de apparaten in een specifieke laboratoriumomgeving. Alle apparaten die in dit document worden beschreven, hadden een opgeschoonde (standaard)configuratie. Als uw netwerk live is, moet u de potentiële impact van elke opdracht begrijpen.

Conventies

Raadpleeg Cisco Technical Tips Conventions (Conventies voor technische tips van Cisco) voor meer informatie over documentconventies.

Tractieprocedure

Kijk voor routers voor de cisco-EnvProRedundantSupplynotification-trap van de CISCO-ENVMON-MIB MIB. De variabelen ciscoEnvSupplyDescr en ciscoEnvSupplyState geven details over de aard van de verandering. U dient de snmp-server aan te passen, zet de opdracht vallen op om vallen in te schakelen.

.1.3.6.1.4.1.9.9.13.3.0.5

ciscoEnvMonRedundantSupplyNotification OBJECT-TYPE

-- FROM CISCO-ENVMON-MIB TRAP VARBINDS { ciscoEnvMonSupplyStatusDescr, ciscoEnvMonSupplyState }

DESCRIPTION "A ciscoEnvMonRedundantSupplyNotification is sent if the redundant power supply

(where extant) fails. Since such a

notification is usually generated before the shutdown state is reached, it can convey more data

and has a better chance of being sent than does the

ciscoEnvMonShutdownNotification."

::= { iso(1) org(3) dod(6) internet(1) private(4) enterprises(1) cisco(9) ciscoMgmt(9) ciscoEnvMonMIB(13)

ciscoEnvMonMIBNotificationPrefix(3)ciscoEnvMonMIBNotifications(0) 5 }

.1.3.6.1.4.1.9.9.13.1.5.1.2

ciscoEnvMonSupplyStatusDescr OBJECT-TYPE

-- FROM CISCO-ENVMON-MIB

-- TEXTUAL CONVENTION DisplayString

SYNTAX OCTET STRING (0..32) DISPLAY-HINT "255a"

MAX-ACCESS read-only

STATUS Current

DESCRIPTION "Textual description of the power supply being instrumented. This description is a

short textual label, suitable as a

human-sensible identification for the rest of the information in the entry."

::= { ISO(1) org(3) DOD(6) Internet(1) private(4) enterprises(1) cisco(9) ciscoMgmt(9)

ciscoEnvMonMIB(13) ciscoEnvMonObjects(1)

ciscoEnvMonSupplyStatusTable(5) ciscoEnvMonSupplyStatusEntry(1) 2 }

.1.3.6.1.4.1.9.9.13.1.5.1.3 ciscoEnvMonSupplyState OBJECT-TYPE

-- FROM CISCO-ENVMON-MIB

-- TEXTUAL CONVENTION CiscoEnvMonState

SYNTAX Integer { normal(1), warning(2), critical(3), shutdown(4), notPresent(5) }

MAX-ACCESS read-only

STATUS Current

DESCRIPTION "The current state of the power supply being instrumented."

::= { ISO(1) org(3) DOD(6) Internet(1) private(4) enterprises(1) cisco(9) ciscoMgmt(9)

ciscoEnvMonMIB(13) ciscoEnvMonObjects(1)

ciscoEnvMonSupplyStatusTable(5) ciscoEnvMonSupplyStatusEntry(1) 3 }

Kijk voor switches voor de SNMP-trap ChassisAlarmOn. De variabelen chassisTempAlarm, chassisMinorAlarm en chassisMajorAlarm zijn opgenomen met de val en zijn noodzakelijk voor het bepalen van het specifieke chassis alarm dat in uitvoering is. Al deze vallen komen van de CISCO-STACK-MIB.

.1.3.6.1.4.1.9.5.0.5 chassisAlarmOn OBJECT-TYPE

-- FROM CISCO-STACK-MIB TRAP VARBINDS { chassisTempAlarm, chassisMinorAlarm, chassisMajorAlarm }

DESCRIPTION "A chassisAlarmOn trap signifies that the agent entity has detected the chassisTempAlarm,

chassisMinorAlarm, or

chassisMajorAlarm object in this MIB has transitioned to the on(2) state. The generation of this trap

can be controlled by the

sysEnableChassisTraps object in this MIB."

::= { ISO(1) org(3) DOD(6) Internet(1) private(4) enterprises(1) cisco(9) workgroup(5)

ciscoStackNotificationsPrefix(0) 5 }

.1.3.6.1.4.1.9.5.1.2.13 chassisTempAlarm OBJECT-TYPE

-- FROM CISCO-STACK-MIB SYNTAX Integer { off(1), on(2), critical(3) }

MAX-ACCESS read-only

STATUS Current

DESCRIPTION "The chassis temperature alarm status."

::= { ISO(1) org(3) DOD(6) Internet(1) private(4) enterprises(1) cisco(9) workgroup(5) ciscoStackMIB(1)

chassisGrp(2) 13 }

.1.3.6.1.4.1.9.5.1.2.11 chassisMinorAlarm OBJECT-TYPE

-- FROM CISCO-STACK-MIB SYNTAX Integer { off(1), on(2) }

MAX-ACCESS read-only

STATUS Current

DESCRIPTION "The chassis minor alarm status."

::= { ISO(1) org(3) DOD(6) Internet(1) private(4) enterprises(1) cisco(9) workgroup(5) ciscoStackMIB(1)

chassisGrp(2) 11 }

.1.3.6.1.4.1.9.5.1.2.12 chassisMajorAlarm OBJECT-TYPE

-- FROM CISCO-STACK-MIB

SYNTAX Integer { off(1), on(2) }

MAX-ACCESS read-only

STATUS Current

DESCRIPTION "The chassis major alarm status."

::= { ISO(1) org(3) DOD(6) Internet(1) private(4) enterprises(1) cisco(9) workgroup(5) ciscoStackMIB(1)

chassisGrp(2) 12 }

Gerelateerde informatie

- Eenvoudige netwerkbeheerprotocolondersteuning

- Technische ondersteuning - Cisco-systemen