목차

소개

사전 요구 사항

요구 사항

사용되는 구성 요소

표기 규칙

추적 절차

관련 정보

소개

디바이스에 예비 전원 공급 장치가 포함된 경우 전원 공급 장치 중 하나가 중단되거나 상태가 변경될 때 디바이스에서 트랩을 생성하도록 선택할 수 있습니다.라우터와 스위치 모두에 트랩이 존재하며 상태 변경 또는 실패를 알리고 변경 특성에 대한 추가 정보를 가리킵니다.이 문서에서는 SNMP(Simple Network Management Protocol)를 사용하여 예비 전원 공급 장치 중 하나가 중단되거나 상태가 변경되는 경우를 추적하는 방법에 대해 설명합니다.

사전 요구 사항

요구 사항

이 문서에 대한 특정 요건이 없습니다.

사용되는 구성 요소

이 문서의 정보는 예비 전원 공급 장치가 있는 Cisco 라우터 및 스위치에 유효합니다.

이 문서의 정보는 특정 랩 환경의 디바이스를 토대로 작성되었습니다.이 문서에 사용된 모든 디바이스는 초기화된(기본) 컨피그레이션으로 시작되었습니다.현재 네트워크가 작동 중인 경우, 모든 명령어의 잠재적인 영향을 미리 숙지하시기 바랍니다.

표기 규칙

문서 규칙에 대한 자세한 내용은 Cisco 기술 팁 표기 규칙을 참조하십시오.

추적 절차

라우터의 경우 CISCO-ENVMON-MIB MIB에서 ciscoEnvMonRedundantSupplyNotification 트랩을 확인합니다.ciscoEnvMonSupplyDescr 및 ciscoEnvMonSupplyState 변수는 변경의 특성에 대한 세부 정보를 제공합니다.트랩을 활성화하려면 snmp-server enable traps envmon 명령을 구성해야 합니다.

.1.3.6.1.4.1.9.9.13.3.0.5

ciscoEnvMonRedundantSupplyNotification OBJECT-TYPE

-- FROM CISCO-ENVMON-MIB TRAP VARBINDS { ciscoEnvMonSupplyStatusDescr, ciscoEnvMonSupplyState }

DESCRIPTION "A ciscoEnvMonRedundantSupplyNotification is sent if the redundant power supply

(where extant) fails. Since such a

notification is usually generated before the shutdown state is reached, it can convey more data

and has a better chance of being sent than does the

ciscoEnvMonShutdownNotification."

::= { iso(1) org(3) dod(6) internet(1) private(4) enterprises(1) cisco(9) ciscoMgmt(9) ciscoEnvMonMIB(13)

ciscoEnvMonMIBNotificationPrefix(3)ciscoEnvMonMIBNotifications(0) 5 }

.1.3.6.1.4.1.9.9.13.1.5.1.2

ciscoEnvMonSupplyStatusDescr OBJECT-TYPE

-- FROM CISCO-ENVMON-MIB

-- TEXTUAL CONVENTION DisplayString

SYNTAX OCTET STRING (0..32) DISPLAY-HINT "255a"

MAX-ACCESS read-only

STATUS Current

DESCRIPTION "Textual description of the power supply being instrumented. This description is a

short textual label, suitable as a

human-sensible identification for the rest of the information in the entry."

::= { ISO(1) org(3) DOD(6) Internet(1) private(4) enterprises(1) cisco(9) ciscoMgmt(9)

ciscoEnvMonMIB(13) ciscoEnvMonObjects(1)

ciscoEnvMonSupplyStatusTable(5) ciscoEnvMonSupplyStatusEntry(1) 2 }

.1.3.6.1.4.1.9.9.13.1.5.1.3 ciscoEnvMonSupplyState OBJECT-TYPE

-- FROM CISCO-ENVMON-MIB

-- TEXTUAL CONVENTION CiscoEnvMonState

SYNTAX Integer { normal(1), warning(2), critical(3), shutdown(4), notPresent(5) }

MAX-ACCESS read-only

STATUS Current

DESCRIPTION "The current state of the power supply being instrumented."

::= { ISO(1) org(3) DOD(6) Internet(1) private(4) enterprises(1) cisco(9) ciscoMgmt(9)

ciscoEnvMonMIB(13) ciscoEnvMonObjects(1)

ciscoEnvMonSupplyStatusTable(5) ciscoEnvMonSupplyStatusEntry(1) 3 }

스위치의 경우 SNMP 트랩 섀시AlarmOn을 확인합니다.chassisTempAlarm, chassisMinorAlarm 및 chassisMajorAlarm 변수가 트랩에 포함되며 진행 중인 특정 섀시 알람을 확인하는 데 필요합니다.이러한 모든 트랩은 CISCO-STACK-MIB에서 가져옵니다.

.1.3.6.1.4.1.9.5.0.5 chassisAlarmOn OBJECT-TYPE

-- FROM CISCO-STACK-MIB TRAP VARBINDS { chassisTempAlarm, chassisMinorAlarm, chassisMajorAlarm }

DESCRIPTION "A chassisAlarmOn trap signifies that the agent entity has detected the chassisTempAlarm,

chassisMinorAlarm, or

chassisMajorAlarm object in this MIB has transitioned to the on(2) state. The generation of this trap

can be controlled by the

sysEnableChassisTraps object in this MIB."

::= { ISO(1) org(3) DOD(6) Internet(1) private(4) enterprises(1) cisco(9) workgroup(5)

ciscoStackNotificationsPrefix(0) 5 }

.1.3.6.1.4.1.9.5.1.2.13 chassisTempAlarm OBJECT-TYPE

-- FROM CISCO-STACK-MIB SYNTAX Integer { off(1), on(2), critical(3) }

MAX-ACCESS read-only

STATUS Current

DESCRIPTION "The chassis temperature alarm status."

::= { ISO(1) org(3) DOD(6) Internet(1) private(4) enterprises(1) cisco(9) workgroup(5) ciscoStackMIB(1)

chassisGrp(2) 13 }

.1.3.6.1.4.1.9.5.1.2.11 chassisMinorAlarm OBJECT-TYPE

-- FROM CISCO-STACK-MIB SYNTAX Integer { off(1), on(2) }

MAX-ACCESS read-only

STATUS Current

DESCRIPTION "The chassis minor alarm status."

::= { ISO(1) org(3) DOD(6) Internet(1) private(4) enterprises(1) cisco(9) workgroup(5) ciscoStackMIB(1)

chassisGrp(2) 11 }

.1.3.6.1.4.1.9.5.1.2.12 chassisMajorAlarm OBJECT-TYPE

-- FROM CISCO-STACK-MIB

SYNTAX Integer { off(1), on(2) }

MAX-ACCESS read-only

STATUS Current

DESCRIPTION "The chassis major alarm status."

::= { ISO(1) org(3) DOD(6) Internet(1) private(4) enterprises(1) cisco(9) workgroup(5) ciscoStackMIB(1)

chassisGrp(2) 12 }

관련 정보

- Simple Network Management Protocol 지원 리소스

- Technical Support - Cisco Systems