목차

소개

사전 요구 사항

요구 사항

사용되는 구성 요소

표기 규칙

절차

CISCO-ENTITY-SENSOR-MIB의 OID 개요

ENTITY-MIB의 OID 개요

CLI를 통한 show environment temperature 명령의 출력

문제 해결

스위치에서 ciscoEnvMonTemperatureStatusDescr=module[no] 전송

관련 정보

소개

이 문서에서는 Cisco Catalyst 6500/6000의 온도 값을 가져오는 프로세스에 대해 설명합니다. SNMP(Simple Network Management Protocol)를 사용하는 show environment temperature CLI(command-line interface) 명령은 이러한 값을 표시합니다.

사전 요구 사항

요구 사항

이 문서에 대한 특정 요건이 없습니다.

사용되는 구성 요소

이 문서의 정보는 다음 소프트웨어 및 하드웨어 버전을 기반으로 합니다.

- Catalyst 6500/6000 시리즈 스위치:

- Catalyst OS(CatOS)를 실행하는 Catalyst OS - CISCO-ENTITY-SENSOR-MIB를 초기 Supervisor Engine 모듈 소프트웨어 버전으로 지원합니다.

Catalyst 6000 및 7600 Catalyst OS MIB 지원 목록을 참조하십시오.

- Cisco IOS® Software 실행 - Cisco IOS Software 릴리스 12.1(8a)EX를 기준으로 CISCO-ENTITY-SENSOR-MIB를 지원합니다.

확인은 Catalyst 6000 및 7600 Cisco IOS MIB 지원 목록을 참조하십시오.

참고: 디바이스 1 및 디바이스 2 센서는 Cisco IOS Software 릴리스 12.1(14)E부터 지원됩니다.이 문서의 CLI 섹션을 통해 show environment temperature 명령의 출력을 참조하십시오.

- CatOS 릴리스 5.5.7

- Sun Solaris 2.7에 설치된 HP OpenView Network Node Manager의 SNMPWalk

이 목적으로 Net-SNMP의 SNMP 유틸리티를 사용할 수도 있습니다.

참고: 이 문서에서는 다음 MIB를 사용합니다.

- CISCO-ENTITY-SENSOR-MIB

- ENTITY-MIB-V1SMI

이 문서의 정보는 특정 랩 환경의 디바이스를 토대로 작성되었습니다.이 문서에 사용된 모든 디바이스는 초기화된(기본) 컨피그레이션으로 시작되었습니다.현재 네트워크가 작동 중인 경우, 모든 명령어의 잠재적인 영향을 미리 숙지하시기 바랍니다.

표기 규칙

문서 규칙에 대한 자세한 내용은 Cisco 기술 팁 표기 규칙을 참고하십시오.

절차

다음 단계를 완료하십시오.

1. OID(object identifier) entSensorValue(1.3.6.1.4.1.9.9.91.1.1.1.1.4)를 사용하여 온도 값을 가져옵니다.

이 OID는 CISCO-ENTITY-SENSOR-MIB에서 가져옵니다.이 MIB와 관련된 다른 모든 OID에 대해서는 이 문서의 CISCO-ENTITY-SENSOR-MIB의 OID 개요 섹션을 참조하십시오.MIB는 다음 설명을 제공합니다.

entSensorValue OBJECT-TYPE

SYNTAX SensorValue

--    Rsyntax INTEGER(-1000000000..1000000000)

ACCESS read-only

STATUS mandatory

DESCRIPTION

"This variable reports the most recent measurement seen

by the sensor.

To correctly display or interpret this variable's value,

you must also know entSensorType, entSensorScale, and

entSensorPrecision.

However, you can compare entSensorValue with the threshold

values given in entSensorThresholdTable without any semantic

knowledge."

::= { entSensorValueEntry 4 }

entSensorValue(1.3.6.1.4.1.9.9.91.1.1.1.1.4)에 대한 디바이스를 쿼리합니다. 이 예에서 디바이스 호스트 이름은 zatar입니다.

#snmpwalk -c public zatar 1.3.6.1.4.1.9.9.91.1.1.1.1.4

9.9.91.1.1.1.1.4.15 : INTEGER: 1

9.9.91.1.1.1.1.4.16 : INTEGER: 1

9.9.91.1.1.1.1.4.17 : INTEGER: 2

9.9.91.1.1.1.1.4.18 : INTEGER: 1

9.9.91.1.1.1.1.4.19 : INTEGER: 20

9.9.91.1.1.1.1.4.20 : INTEGER: 1

9.9.91.1.1.1.1.4.21 : INTEGER: 21

9.9.91.1.1.1.1.4.22 : INTEGER: 1

9.9.91.1.1.1.1.4.23 : INTEGER: 20

9.9.91.1.1.1.1.4.1001 : INTEGER: 19

9.9.91.1.1.1.1.4.1002 : INTEGER: 28

9.9.91.1.1.1.1.4.1003 : INTEGER: 22

9.9.91.1.1.1.1.4.1004 : INTEGER: 28

9.9.91.1.1.1.1.4.1007 : INTEGER: 19

9.9.91.1.1.1.1.4.1008 : INTEGER: 23

9.9.91.1.1.1.1.4.1009 : INTEGER: 0

9.9.91.1.1.1.1.4.1010 : INTEGER: 0

9.9.91.1.1.1.1.4.2001 : INTEGER: 16

9.9.91.1.1.1.1.4.2002 : INTEGER: 25

9.9.91.1.1.1.1.4.2003 : INTEGER: 26

9.9.91.1.1.1.1.4.2004 : INTEGER: 0

9.9.91.1.1.1.1.4.3001 : INTEGER: 17

9.9.91.1.1.1.1.4.3002 : INTEGER: 20

9.9.91.1.1.1.1.4.3003 : INTEGER: 19

9.9.91.1.1.1.1.4.3004 : INTEGER: 24

9.9.91.1.1.1.1.4.4001 : INTEGER: 25

9.9.91.1.1.1.1.4.4002 : INTEGER: 29

9.9.91.1.1.1.1.4.4003 : INTEGER: 0

9.9.91.1.1.1.1.4.4004 : INTEGER: 0

9.9.91.1.1.1.1.4.5001 : INTEGER: 20

9.9.91.1.1.1.1.4.5002 : INTEGER: 20

9.9.91.1.1.1.1.4.5003 : INTEGER: 0

9.9.91.1.1.1.1.4.5004 : INTEGER: 0

#

2. 모든 온도 값을 Catalyst의 올바른 모듈에 연결하는 방법을 결정합니다.

예를 들어, 인덱스는 9.9.91.1.1.1.1.4.1001에서 무엇을 수행합니까?정수:19개 줄까요?알아내기 위해서는 한 단계 올라가야 합니다.1.3.6.1.4.1.9.9.91.1.1.1.1.4에서 1.3.6.1.4.1.9.9.91.1.1.1.1으로 한 단계 뛰어4를 끝에 놓습니다.이렇게 하면 entSensorValueEntry(1.3.6.1.4.1.9.9.91.1.1.1.1)으로 이동합니다. MIB는 다음 설명을 제공합니다.

entSensorValueEntry OBJECT-TYPE

SYNTAX EntSensorValueEntry

ACCESS not-accessible

STATUS mandatory

DESCRIPTION

"An entSensorValueTable entry describes the

present reading of a sensor, the measurement units

and scale, and sensor operational status."

INDEX { entPhysicalIndex }

::= { entSensorValueTable 1 }

설명에서는 이 OID가 snmpwalk 1001, 1002 등에서 볼 수 있는 것처럼 인덱스를 사용한다는 것을 보여줍니다.entSensorValueEntry 설명은 다른 MIB인 ENTITY-MIB를 제공하는 또 다른 OID, entPhysicalIndex를 표시합니다.

IMPORTS

Integer32

FROM SNMPv2-SMI-v1

OBJECT-TYPE

FROM RFC-1212

TRAP-TYPE

FROM RFC-1215

TimeStamp, TruthValue

FROM SNMPv2-TC-v1

entPhysicalIndex

FROM ENTITY-MIB

ciscoMgmt

ent PhysicalIndex는 ENTITY-MIB에서 가져옵니다.ENTITY-MIB는 entPhysicalIndex에 대한 다음 설명을 제공합니다.

entPhysicalEntry ::= SEQUENCE {

entPhysicalIndex PhysicalIndex,

entPhysicalDescr SnmpAdminString,

entPhysicalVendorType AutonomousType,

entPhysicalContainedIn INTEGER,

entPhysicalClass PhysicalClass,

entPhysicalParentRelPos INTEGER,

entPhysicalName SnmpAdminString,

entPhysicalHardwareRev SnmpAdminString,

entPhysicalFirmwareRev SnmpAdminString,

entPhysicalSoftwareRev SnmpAdminString,

entPhysicalSerialNum SnmpAdminString,

entPhysicalMfgName SnmpAdminString,

entPhysicalModelName SnmpAdminString,

entPhysicalAlias SnmpAdminString,

entPhysicalAssetID SnmpAdminString,

entPhysicalIsFRU TruthValue

}

entPhysicalIndex OBJECT-TYPE

SYNTAX PhysicalIndex

--    Rsyntax INTEGER(1..2147483647)

ACCESS not-accessible

STATUS mandatory

DESCRIPTION

"The index for this entry."

::= { entPhysicalEntry 1 }

이 설명에서 트리에서 한 단계 뒤로 다시 이동하여 entPhysicalIndex가 entPhysicalEntry에서 나온다고 결론을 내릴 수 있습니다.

3. entPhysicalIndex(1.3.6.1.2.1.47.1.1.1.1.1)를 쿼리하고 entPhysicalDescr(1.3.6.1.2.1.47.1.1.1.1.2)을 쿼리합니다.

이 명령은 1001, 1002, 1003, 1004 등에 대한 설명을 제공합니다.

#snmpwalk -c public zatar 1.3.6.1.2.1.47.1.1.1.1.2

47.1.1.1.1.2.1 : OCTET STRING- (ascii): Cisco Systems WS-C6506 6 slot switch

47.1.1.1.1.2.2 : OCTET STRING- (ascii): WS-C6506 6 slot switch chassis slot

47.1.1.1.1.2.3 : OCTET STRING- (ascii): WS-C6506 6 slot switch chassis slot

47.1.1.1.1.2.4 : OCTET STRING- (ascii): WS-C6506 6 slot switch chassis slot

47.1.1.1.1.2.5 : OCTET STRING- (ascii): WS-C6506 6 slot switch chassis slot

47.1.1.1.1.2.6 : OCTET STRING- (ascii): WS-C6506 6 slot switch chassis slot

47.1.1.1.1.2.7 : OCTET STRING- (ascii): WS-C6506 6 slot switch chassis slot

47.1.1.1.1.2.8 : OCTET STRING- (ascii): WS-C6506 6 slot switch backplane

47.1.1.1.1.2.9 : OCTET STRING- (ascii): Container of power supply group

47.1.1.1.1.2.10 : OCTET STRING- (ascii):        Container of power supply

47.1.1.1.1.2.11 : OCTET STRING- (ascii):        power supply

47.1.1.1.1.2.12 : OCTET STRING- (ascii):        Container of power supply

47.1.1.1.1.2.14 : OCTET STRING- (ascii):        Container of Fan

47.1.1.1.1.2.15 : OCTET STRING- (ascii):        Fan

47.1.1.1.1.2.16 : OCTET STRING- (ascii):        Clock

47.1.1.1.1.2.17 : OCTET STRING- (ascii):        Clock

47.1.1.1.1.2.18 : OCTET STRING- (ascii):        VTT

47.1.1.1.1.2.19 : OCTET STRING- (ascii):        VTT Temp Sensor

47.1.1.1.1.2.20 : OCTET STRING- (ascii):        VTT

47.1.1.1.1.2.21 : OCTET STRING- (ascii):        VTT Temp Sensor

47.1.1.1.1.2.22 : OCTET STRING- (ascii):        VTT

47.1.1.1.1.2.23 : OCTET STRING- (ascii):        VTT Temp Sensor

47.1.1.1.1.2.1000 : OCTET STRING- (ascii):      WS-X6K-SUP1A-2GE 1000BaseX

Supervisor Rev. 3.1

47.1.1.1.1.2.1001 : OCTET STRING- (ascii):      Module Intake Temp Sensor

47.1.1.1.1.2.1002 : OCTET STRING- (ascii):      Module Exhaust Temp Sensor

47.1.1.1.1.2.1003 : OCTET STRING- (ascii):      Module  Device 1 Temp Sensor

47.1.1.1.1.2.1004 : OCTET STRING- (ascii):      Module  Device 2 Temp Sensor

47.1.1.1.1.2.1005 : OCTET STRING- (ascii):      L3 Switching Engine Container

47.1.1.1.1.2.1006 : OCTET STRING- (ascii):      L3 Switching Engine

47.1.1.1.1.2.1007 : OCTET STRING- (ascii):      L3 SE Intake Temp Sensor

47.1.1.1.1.2.1008 : OCTET STRING- (ascii):      L3 SE Exhaust Temp Sensor

47.1.1.1.1.2.1009 : OCTET STRING- (ascii):      L3 SE device1 Temp Sensor

47.1.1.1.1.2.1010 : OCTET STRING- (ascii):      L3 SE device2 Temp Sensor

47.1.1.1.1.2.1011 : OCTET STRING- (ascii):      CPU of supervisor

47.1.1.1.1.2.1012 : OCTET STRING- (ascii):      Ethernet Gigabit port interface

47.1.1.1.1.2.1013 : OCTET STRING- (ascii):      Ethernet Gigabit port interface

47.1.1.1.1.2.1014 : OCTET STRING- (ascii):      Container of Router Switch

Feature Card

47.1.1.1.1.2.2000 : OCTET STRING- (ascii):      WS-X6182-2PA FlexWAN Module Rev.

1.3

47.1.1.1.1.2.2001 : OCTET STRING- (ascii):      Module Intake Temp Sensor

47.1.1.1.1.2.2002 : OCTET STRING- (ascii):      Module Exhaust Temp Sensor

47.1.1.1.1.2.2003 : OCTET STRING- (ascii):      Module  Device 1 Temp Sensor

47.1.1.1.1.2.2004 : OCTET STRING- (ascii):      Module  Device 2 Temp Sensor

47.1.1.1.1.2.3000 : OCTET STRING- (ascii):      WS-X6248-RJ-45 10/100BaseTX

Ethernet Rev. 1.1

47.1.1.1.1.2.3001 : OCTET STRING- (ascii):      Module Intake Temp Sensor

47.1.1.1.1.2.3002 : OCTET STRING- (ascii):      Module Exhaust Temp Sensor

47.1.1.1.1.2.3003 : OCTET STRING- (ascii):      Module  Device 1 Temp Sensor

47.1.1.1.1.2.3004 : OCTET STRING- (ascii):      Module  Device 2 Temp Sensor

47.1.1.1.1.2.3005 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3006 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3007 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3008 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3009 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3010 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3011 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3012 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3013 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3014 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3015 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3016 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3017 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3018 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3019 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3020 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3021 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3022 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3023 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3024 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3025 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3026 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3027 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3028 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3029 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3030 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3031 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3032 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3033 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3034 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3035 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3036 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3037 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3038 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3039 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3040 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3041 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3042 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3043 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3044 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3045 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3046 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3047 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3048 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3049 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3050 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3051 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3052 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.4000 : OCTET STRING- (ascii):      Router Switch feature Card

47.1.1.1.1.2.4001 : OCTET STRING- (ascii):      RSFC Intake Temp Sensor

47.1.1.1.1.2.4002 : OCTET STRING- (ascii):      RSFC Temp Sensor

47.1.1.1.1.2.4003 : OCTET STRING- (ascii):      RSFC device1 Temp Sensor

47.1.1.1.1.2.4004 : OCTET STRING- (ascii):      RSFC device2 Temp Sensor

47.1.1.1.1.2.4005 : OCTET STRING- (ascii):      Route Switch

47.1.1.1.1.2.5000 : OCTET STRING- (ascii):      WS-X6380-NAM Network Analysis

Module Rev. 1.1

47.1.1.1.1.2.5001 : OCTET STRING- (ascii):      Module Intake Temp Sensor

47.1.1.1.1.2.5002 : OCTET STRING- (ascii):      Module Exhaust Temp Sensor

47.1.1.1.1.2.5003 : OCTET STRING- (ascii):      Module  Device 1 Temp Sensor

47.1.1.1.1.2.5004 : OCTET STRING- (ascii):      Module  Device 2 Temp Sensor

47.1.1.1.1.2.5005 : OCTET STRING- (ascii):      Net Analysis

47.1.1.1.1.2.5006 : OCTET STRING- (ascii):      Net Analysis

#

이제 색인을 설명에 연결하고 색인을 온도 값에 연결합니다.

4. 온도 값과 설명 사이의 링크를 만듭니다.

3단계에서 이 정보를 추출합니다.

47.1.1.1.1.2.1001 : OCTET STRING- (ascii):      Module Intake Temp Sensor

47.1.1.1.1.2.1002 : OCTET STRING- (ascii):      Module Exhaust Temp Sensor

47.1.1.1.1.2.1003 : OCTET STRING- (ascii):      Module  Device 1 Temp Sensor

47.1.1.1.1.2.1004 : OCTET STRING- (ascii):      Module  Device 2 Temp Sensor

1단계에서 이 정보를 추출합니다.

9.9.91.1.1.1.1.4.1001 : INTEGER: 19

9.9.91.1.1.1.1.4.1002 : INTEGER: 28

9.9.91.1.1.1.1.4.1003 : INTEGER: 22

9.9.91.1.1.1.1.4.1004 : INTEGER: 28

결과는 다음과 같은 이점을 제공합니다.

- 모듈 흡입 온도 센서 = 19C

- 모듈 배기 온도 센서 = 28C

- 모듈 장치 1 온도 센서 = 22C

- 모듈 장치 2 온도 센서 = 28C

CISCO-ENTITY-SENSOR-MIB의 OID 개요

"org"                                   "1.3"

"dod"                                   "1.3.6"

"internet"                              "1.3.6.1"

"directory"                             "1.3.6.1.1"

"mgmt"                                  "1.3.6.1.2"

"experimental"                          "1.3.6.1.3"

"private"                               "1.3.6.1.4"

"enterprises"                           "1.3.6.1.4.1"

"cisco"                                 "1.3.6.1.4.1.9"

"ciscoMgmt"                             "1.3.6.1.4.1.9.9"

"entitySensorMIB"                       "1.3.6.1.4.1.9.9.91"

"entitySensorMIBObjects"                "1.3.6.1.4.1.9.9.91.1"

"entitySensorMIBNotificationPrefix"     "1.3.6.1.4.1.9.9.91.2"

"entitySensorMIBConformance"            "1.3.6.1.4.1.9.9.91.3"

"entSensorValues"                       "1.3.6.1.4.1.9.9.91.1.1"

"entSensorThresholds"                   "1.3.6.1.4.1.9.9.91.1.2"

"entSensorValueTable"                   "1.3.6.1.4.1.9.9.91.1.1.1"

"entSensorValueEntry"                   "1.3.6.1.4.1.9.9.91.1.1.1.1"

"entSensorType"                         "1.3.6.1.4.1.9.9.91.1.1.1.1.1"

"entSensorScale"                        "1.3.6.1.4.1.9.9.91.1.1.1.1.2"

"entSensorPrecision"                    "1.3.6.1.4.1.9.9.91.1.1.1.1.3"

"entSensorValue"                        "1.3.6.1.4.1.9.9.91.1.1.1.1.4"

"entSensorStatus"                       "1.3.6.1.4.1.9.9.91.1.1.1.1.5"

"entSensorValueTimeStamp"               "1.3.6.1.4.1.9.9.91.1.1.1.1.6"

"entSensorValueUpdateRate"              "1.3.6.1.4.1.9.9.91.1.1.1.1.7"

"entSensorThresholdTable"               "1.3.6.1.4.1.9.9.91.1.2.1"

"entSensorThresholdEntry"               "1.3.6.1.4.1.9.9.91.1.2.1.1"

"entSensorThresholdIndex"               "1.3.6.1.4.1.9.9.91.1.2.1.1.1"

"entSensorThresholdSeverity"            "1.3.6.1.4.1.9.9.91.1.2.1.1.2"

"entSensorThresholdRelation"            "1.3.6.1.4.1.9.9.91.1.2.1.1.3"

"entSensorThresholdValue"               "1.3.6.1.4.1.9.9.91.1.2.1.1.4"

"entSensorThresholdEvaluation"          "1.3.6.1.4.1.9.9.91.1.2.1.1.5"

"entSensorThresholdNotificationEnable"  "1.3.6.1.4.1.9.9.91.1.2.1.1.6"

"entitySensorMIBNotifications"          "1.3.6.1.4.1.9.9.91.2"

"entitySensorMIBCompliances"            "1.3.6.1.4.1.9.9.91.3.1"

"entitySensorMIBGroups"                 "1.3.6.1.4.1.9.9.91.3.2"

"entitySensorMIBComplianceV01"          "1.3.6.1.4.1.9.9.91.3.1.1"

"entitySensorValueGroup"                "1.3.6.1.4.1.9.9.91.3.2.1"

"entitySensorThresholdGroup"            "1.3.6.1.4.1.9.9.91.3.2.2"

ENTITY-MIB의 OID 개요

"org"                                   "1.3"

"dod"                                   "1.3.6"

"internet"                              "1.3.6.1"

"directory"                             "1.3.6.1.1"

"mgmt"                                  "1.3.6.1.2"

"experimental"                          "1.3.6.1.4.1"

"private"                               "1.3.6.1.4"

"enterprises"                           "1.3.6.1.4.1"

"mib-2"                                 "1.3.6.1.2.1"

"entityMIB"                             "1.3.6.1.2.1.47"

"entityMIBObjects"                      "1.3.6.1.2.1.47.1"

"entityMIBTraps"                        "1.3.6.1.2.1.47.2"

"entityConformance"                     "1.3.6.1.2.1.47.3"

"entityPhysical"                        "1.3.6.1.2.1.47.1.1"

"entityLogical"                         "1.3.6.1.2.1.47.1.2"

"entityMapping"                         "1.3.6.1.2.1.47.1.3"

"entityGeneral"                         "1.3.6.1.2.1.47.1.4"

"entPhysicalTable"                      "1.3.6.1.2.1.47.1.1.1"

"entPhysicalEntry"                      "1.3.6.1.2.1.47.1.1.1.1"

"entPhysicalIndex"                      "1.3.6.1.2.1.47.1.1.1.1.1"

"entPhysicalDescr"                      "1.3.6.1.2.1.47.1.1.1.1.2"

"entPhysicalVendorType"                 "1.3.6.1.2.1.47.1.1.1.1.3"

"entPhysicalContainedIn"                "1.3.6.1.2.1.47.1.1.1.1.4"

"entPhysicalClass"                      "1.3.6.1.2.1.47.1.1.1.1.5"

"entPhysicalParentRelPos"               "1.3.6.1.2.1.47.1.1.1.1.6"

"entPhysicalName"                       "1.3.6.1.2.1.47.1.1.1.1.7"

"entPhysicalHardwareRev"                "1.3.6.1.2.1.47.1.1.1.1.8"

"entPhysicalFirmwareRev"                "1.3.6.1.2.1.47.1.1.1.1.9"

"entPhysicalSoftwareRev"                "1.3.6.1.2.1.47.1.1.1.1.10"

"entPhysicalSerialNum"                  "1.3.6.1.2.1.47.1.1.1.1.11"

"entPhysicalMfgName"                    "1.3.6.1.2.1.47.1.1.1.1.12"

"entPhysicalModelName"                  "1.3.6.1.2.1.47.1.1.1.1.13"

"entPhysicalAlias"                      "1.3.6.1.2.1.47.1.1.1.1.14"

"entPhysicalAssetID"                    "1.3.6.1.2.1.47.1.1.1.1.15"

"entPhysicalIsFRU"                      "1.3.6.1.2.1.47.1.1.1.1.16"

"entLogicalTable"                       "1.3.6.1.2.1.47.1.2.1"

"entLogicalEntry"                       "1.3.6.1.2.1.47.1.2.1.1"

"entLogicalIndex"                       "1.3.6.1.2.1.47.1.2.1.1.1"

"entLogicalDescr"                       "1.3.6.1.2.1.47.1.2.1.1.2"

"entLogicalType"                        "1.3.6.1.2.1.47.1.2.1.1.3"

"entLogicalCommunity"                   "1.3.6.1.2.1.47.1.2.1.1.4"

"entLogicalTAddress"                    "1.3.6.1.2.1.47.1.2.1.1.5"

"entLogicalTDomain"                     "1.3.6.1.2.1.47.1.2.1.1.6"

"entLogicalContextEngineID"             "1.3.6.1.2.1.47.1.2.1.1.7"

"entLogicalContextName"                 "1.3.6.1.2.1.47.1.2.1.1.8"

"entLPMappingTable"                     "1.3.6.1.2.1.47.1.3.1"

"entAliasMappingTable"                  "1.3.6.1.2.1.47.1.3.2"

"entPhysicalContainsTable"              "1.3.6.1.2.1.47.1.3.3"

"entLPMappingEntry"                     "1.3.6.1.2.1.47.1.3.1.1"

"entLPPhysicalIndex"                    "1.3.6.1.2.1.47.1.3.1.1.1"

"entAliasMappingEntry"                  "1.3.6.1.2.1.47.1.3.2.1"

"entAliasLogicalIndexOrZero"            "1.3.6.1.2.1.47.1.3.2.1.1"

"entAliasMappingIdentifier"             "1.3.6.1.2.1.47.1.3.2.1.2"

"entPhysicalContainsEntry"              "1.3.6.1.2.1.47.1.3.3.1"

"entPhysicalChildIndex"                 "1.3.6.1.2.1.47.1.3.3.1.1"

"entLastChangeTime"                     "1.3.6.1.2.1.47.1.4.1"

"entityMIBTrapPrefix"                   "1.3.6.1.2.1.47.2"

"entityCompliances"                     "1.3.6.1.2.1.47.3.1"

"entityGroups"                          "1.3.6.1.2.1.47.3.2"

"entityCompliance"                      "1.3.6.1.2.1.47.3.1.1"

"entity2Compliance"                     "1.3.6.1.2.1.47.3.1.2"

"entityPhysicalGroup"                   "1.3.6.1.2.1.47.3.2.1"

"entityLogicalGroup"                    "1.3.6.1.2.1.47.3.2.2"

"entityMappingGroup"                    "1.3.6.1.2.1.47.3.2.3"

"entityGeneralGroup"                    "1.3.6.1.2.1.47.3.2.4"

"entityPhysical2Group"                  "1.3.6.1.2.1.47.3.2.6"

"entityLogical2Group"                   "1.3.6.1.2.1.47.3.2.7"

"entityNotificationsGroup"              "1.3.6.1.2.1.47.3.2.5"

CLI를 통한 show environment temperature 명령의 출력

참고: show environment temperature 명령을 실행하려면 활성화 모드에 있어야 합니다.

zatar> (enable)#show environment temperature

Intake        Exhaust       Device 1     Device 2

Slot             Temperature   Temperature   Temperature   Temperature

---------------  ------------  ------------  ------------  ------------

1                19C(50C,65C)  28C(60C,75C)  21C           27C

2                20C(50C,65C)  20C(60C,75C)  N/A           N/A

3                16C(50C,65C)  25C(60C,75C)  26C(70C,85C)  N/A

4                17C(50C,65C)  20C(60C,75C)  19C           24C

1  (Switch-Eng)  19C(50C,65C)  23C(60C,75C)  N/A           N/A

1  (MSFC)        24C(50C,65C)  29C(60C,75C)  N/A           N/A

Chassis Modules

------------------

VTT1: 20C(85C,100C)

VTT2: 21C(85C,100C)

VTT3: 19C(85C,100C)

zatar> (enable)

문제 해결

스위치에서 ciscoEnvMonTemperatureStatusDescr=module[no] 전송

스위치는 지정된 테스트 지점에서 측정된 온도가 테스트 지점의 정상 범위를 벗어난다는 알림으로 SNMP ciscoEnvMonTemperatureStatusDescr=Module [no] 메시지를 보냅니다.범위는 다음 단계 중 하나일 수 있습니다.

- 경고

- 중요

- 셧다운

SNMP 알림 트랩의 현재 상태 범위 옵션은 모듈이 제공하는 이러한 세 가지 온도 범위 중 어느 것을 지정합니다.SNMP 알림 트랩의 check duration 옵션은 스위치의 온도가 정상 범위보다 높은 기간을 지정합니다.

모듈의 테스트 지점에서 온도의 현재 상태가 종료 단계에 있는 경우 스위치는 모듈을 자동으로 종료합니다.ciscoEnvMonTemperatureStatusDescr = module[no] 메시지는 정보 메시지입니다.

예기치 않은 문제를 방지하기 위해 권장되는 해결 방법은 모듈 사양에서 지정한 운영 표준 내에 스위치 주변의 온도가 유지되도록 하는 것입니다.이 온도를 결정하려면 이 문서의 CLI 섹션을 통해 show environment temperature 명령의 출력을 참조하십시오.또한 스위치의 내부 팬이 정상적으로 작동하는지 확인합니다.

관련 정보

- IP 애플리케이션 서비스 설계 기술 노트

- 환경 모니터링 스위치 관리

- 기술 지원 및 문서 − Cisco Systems