المحتويات

المقدمة

المتطلبات الأساسية

المتطلبات

المكونات المستخدمة

الاصطلاحات

الإجراء

نظرة عامة على OIDs في Cisco-entity-sensor-MIB

نظرة عامة على OIDs في ENTITY-MIB

إخراج الأمر show environment temperature من خلال CLI

استكشاف الأخطاء وإصلاحها

يرسل المحول CiscoEnvMonTemperatureStatusDescr=module[no]

معلومات ذات صلة

المقدمة

يشرح هذا المستند عملية الحصول على قيم درجة الحرارة الخاصة ب Cisco Catalyst 6500/6000. يعرض أمر واجهة سطر الأوامر (CLI) show environment temperature، مع إستخدام بروتوكول إدارة الشبكة البسيط (SNMP)، هذه القيم.

المتطلبات الأساسية

المتطلبات

لا توجد متطلبات خاصة لهذا المستند.

المكونات المستخدمة

تستند المعلومات الواردة في هذا المستند إلى إصدارات البرامج والمكونات المادية التالية:

- مُحوّلات Catalyst 6500/6000 Series Switches:

- أن يركض مادة حفازة os (CatOS)—يساند Cisco-entity-sensor-MIB مثل الأولي مشرف محرك وحدة نمطية صيغة برمجية.

ارجع إلى قائمة دعم قاعدة معلومات الإدارة (MIB) لنظام التشغيل Catalyst 6000 و 7600.

- التي تشغل برنامج Cisco IOS® — دعم Cisco-entity-sensor-MIB كما هو الحال في برنامج Cisco IOS الإصدار 12.1(8a)EX.

ارجع إلى قائمة دعم Catalyst 6000 و 7600 Cisco IOS MIB للتحقق.

ملاحظة: دعم أجهزة إستشعار الجهاز 1 والجهاز 2 بدءا من برنامج Cisco IOS الإصدار 12.1(14)E. رأيت الإنتاج من العرض بيئة درجة حرارة أمر من خلال ال CLI قسم من هذا وثيقة.

- CatOS، الإصدار 5.5.7

- برنامج SNMPalk من برنامج OpenView Network Node Manager من HP المثبت على نظام التشغيل Sun Solaris 2.7

يمكنك أيضا إستخدام أدوات مساعدة SNMP من Net-SNMP لهذا الغرض.

ملاحظة: يستخدم هذا المستند قواعد معلومات الإدارة (MIB) التالية:

- Cisco-entity-sensor-MIB

- ENTITY-MIB-V1SMI

تم إنشاء المعلومات الواردة في هذا المستند من الأجهزة الموجودة في بيئة معملية خاصة. بدأت جميع الأجهزة المُستخدمة في هذا المستند بتكوين ممسوح (افتراضي). إذا كانت شبكتك مباشرة، فتأكد من فهمك للتأثير المحتمل لأي أمر.

الاصطلاحات

راجع اصطلاحات تلميحات Cisco التقنية للحصول على مزيد من المعلومات حول اصطلاحات المستندات.

الإجراء

أكمل الخطوات التالية:

1. أستخدم معرف الكائن (OID) entSensorValue (1.3.6.1.4.1.9.91.1.1.1.4) للحصول على قيم درجة الحرارة.

يأتي هذا المعرف من Cisco-entity-sensor-mib. لجميع OIDs الأخرى التي تتعلق ب MIB هذا، راجع نظرة عامة على OIDs في قسم cisco-entity-sensor-mib في هذا المستند. توفر قاعدة معلومات الإدارة هذا الوصف:

entSensorValue OBJECT-TYPE

SYNTAX SensorValue

--    Rsyntax INTEGER(-1000000000..1000000000)

ACCESS read-only

STATUS mandatory

DESCRIPTION

"This variable reports the most recent measurement seen

by the sensor.

To correctly display or interpret this variable's value,

you must also know entSensorType, entSensorScale, and

entSensorPrecision.

However, you can compare entSensorValue with the threshold

values given in entSensorThresholdTable without any semantic

knowledge."

::= { entSensorValueEntry 4 }

الاستعلام عن الجهاز ل entSensorValue (1.3.6.1.4.1.9.91.1.1.1.1.4). في هذا المثال، اسم مضيف الجهاز هو zatar:

#snmpwalk -c public zatar 1.3.6.1.4.1.9.9.91.1.1.1.1.4

9.9.91.1.1.1.1.4.15 : INTEGER: 1

9.9.91.1.1.1.1.4.16 : INTEGER: 1

9.9.91.1.1.1.1.4.17 : INTEGER: 2

9.9.91.1.1.1.1.4.18 : INTEGER: 1

9.9.91.1.1.1.1.4.19 : INTEGER: 20

9.9.91.1.1.1.1.4.20 : INTEGER: 1

9.9.91.1.1.1.1.4.21 : INTEGER: 21

9.9.91.1.1.1.1.4.22 : INTEGER: 1

9.9.91.1.1.1.1.4.23 : INTEGER: 20

9.9.91.1.1.1.1.4.1001 : INTEGER: 19

9.9.91.1.1.1.1.4.1002 : INTEGER: 28

9.9.91.1.1.1.1.4.1003 : INTEGER: 22

9.9.91.1.1.1.1.4.1004 : INTEGER: 28

9.9.91.1.1.1.1.4.1007 : INTEGER: 19

9.9.91.1.1.1.1.4.1008 : INTEGER: 23

9.9.91.1.1.1.1.4.1009 : INTEGER: 0

9.9.91.1.1.1.1.4.1010 : INTEGER: 0

9.9.91.1.1.1.1.4.2001 : INTEGER: 16

9.9.91.1.1.1.1.4.2002 : INTEGER: 25

9.9.91.1.1.1.1.4.2003 : INTEGER: 26

9.9.91.1.1.1.1.4.2004 : INTEGER: 0

9.9.91.1.1.1.1.4.3001 : INTEGER: 17

9.9.91.1.1.1.1.4.3002 : INTEGER: 20

9.9.91.1.1.1.1.4.3003 : INTEGER: 19

9.9.91.1.1.1.1.4.3004 : INTEGER: 24

9.9.91.1.1.1.1.4.4001 : INTEGER: 25

9.9.91.1.1.1.1.4.4002 : INTEGER: 29

9.9.91.1.1.1.1.4.4003 : INTEGER: 0

9.9.91.1.1.1.1.4.4004 : INTEGER: 0

9.9.91.1.1.1.1.4.5001 : INTEGER: 20

9.9.91.1.1.1.1.4.5002 : INTEGER: 20

9.9.91.1.1.1.1.4.5003 : INTEGER: 0

9.9.91.1.1.1.1.4.5004 : INTEGER: 0

#

2. حدد كيفية ربط كل قيم درجات الحرارة بالوحدة النمطية الصحيحة في المادة حفازة.

على سبيل المثال، ما هو الرقم القياسي 9.9.91.1.1.1.4.1001: عدد صحيح: 19 رمز؟ لمعرفة ذلك، يجب أن ترتقي بمستوى واحد في الشجرة. انقل مستوى واحد من 1.3.6.1.4.1.9.91.1.1.1.4 مرة أخرى إلى 1.3.6.1.4.1.9.91.1.1.1.1؛ قم بإسقاط المستوى 4 في النهاية. وهذا ينقلك إلى EntSensorValueEntry (1.3.6.1.4.1.9.91.1.1.1.1). توفر قاعدة معلومات الإدارة هذا الوصف:

entSensorValueEntry OBJECT-TYPE

SYNTAX EntSensorValueEntry

ACCESS not-accessible

STATUS mandatory

DESCRIPTION

"An entSensorValueTable entry describes the

present reading of a sensor, the measurement units

and scale, and sensor operational status."

INDEX { entPhysicalIndex }

::= { entSensorValueTable 1 }

يوضح الوصف أن هذا المعرف الشخصي يستخدم فهارس، كما ترى في Snmpwalk 1001 و 1002 وما إلى ذلك. يوضح وصف entSensorValueEntry معرف فريد (OID) آخر، entPhysicalIndex، والذي يوفر قاعدة معلومات إدارة (MIB) أخرى، وهي ENTITY-MIB.

IMPORTS

Integer32

FROM SNMPv2-SMI-v1

OBJECT-TYPE

FROM RFC-1212

TRAP-TYPE

FROM RFC-1215

TimeStamp, TruthValue

FROM SNMPv2-TC-v1

entPhysicalIndex

FROM ENTITY-MIB

ciscoMgmt

يأتي entPhysicalIndex من entity-mib. يوفر ENTITY-MIB هذا الوصف ل entPhysicalIndex:

entPhysicalEntry ::= SEQUENCE {

entPhysicalIndex PhysicalIndex,

entPhysicalDescr SnmpAdminString,

entPhysicalVendorType AutonomousType,

entPhysicalContainedIn INTEGER,

entPhysicalClass PhysicalClass,

entPhysicalParentRelPos INTEGER,

entPhysicalName SnmpAdminString,

entPhysicalHardwareRev SnmpAdminString,

entPhysicalFirmwareRev SnmpAdminString,

entPhysicalSoftwareRev SnmpAdminString,

entPhysicalSerialNum SnmpAdminString,

entPhysicalMfgName SnmpAdminString,

entPhysicalModelName SnmpAdminString,

entPhysicalAlias SnmpAdminString,

entPhysicalAssetID SnmpAdminString,

entPhysicalIsFRU TruthValue

}

entPhysicalIndex OBJECT-TYPE

SYNTAX PhysicalIndex

--    Rsyntax INTEGER(1..2147483647)

ACCESS not-accessible

STATUS mandatory

DESCRIPTION

"The index for this entry."

::= { entPhysicalEntry 1 }

من هذا الوصف، يمكنك مرة أخرى الرجوع خطوة إلى الوراء في الشجرة والاستنتاج أن entPhysicalIndex يأتي من entPhysicalEntry.

3. استعلام عن EntPhysicalIndex (1.3.6.1.2.1.47.1.1.1.1) ثم EntPhysicalDescr (1.3.6.1.2.1.47.1.1.1.2).

يمنحك هذا الأمر وصف من 1001، 1002، 1003، 1004، وهكذا:

#snmpwalk -c public zatar 1.3.6.1.2.1.47.1.1.1.1.2

47.1.1.1.1.2.1 : OCTET STRING- (ascii): Cisco Systems WS-C6506 6 slot switch

47.1.1.1.1.2.2 : OCTET STRING- (ascii): WS-C6506 6 slot switch chassis slot

47.1.1.1.1.2.3 : OCTET STRING- (ascii): WS-C6506 6 slot switch chassis slot

47.1.1.1.1.2.4 : OCTET STRING- (ascii): WS-C6506 6 slot switch chassis slot

47.1.1.1.1.2.5 : OCTET STRING- (ascii): WS-C6506 6 slot switch chassis slot

47.1.1.1.1.2.6 : OCTET STRING- (ascii): WS-C6506 6 slot switch chassis slot

47.1.1.1.1.2.7 : OCTET STRING- (ascii): WS-C6506 6 slot switch chassis slot

47.1.1.1.1.2.8 : OCTET STRING- (ascii): WS-C6506 6 slot switch backplane

47.1.1.1.1.2.9 : OCTET STRING- (ascii): Container of power supply group

47.1.1.1.1.2.10 : OCTET STRING- (ascii):        Container of power supply

47.1.1.1.1.2.11 : OCTET STRING- (ascii):        power supply

47.1.1.1.1.2.12 : OCTET STRING- (ascii):        Container of power supply

47.1.1.1.1.2.14 : OCTET STRING- (ascii):        Container of Fan

47.1.1.1.1.2.15 : OCTET STRING- (ascii):        Fan

47.1.1.1.1.2.16 : OCTET STRING- (ascii):        Clock

47.1.1.1.1.2.17 : OCTET STRING- (ascii):        Clock

47.1.1.1.1.2.18 : OCTET STRING- (ascii):        VTT

47.1.1.1.1.2.19 : OCTET STRING- (ascii):        VTT Temp Sensor

47.1.1.1.1.2.20 : OCTET STRING- (ascii):        VTT

47.1.1.1.1.2.21 : OCTET STRING- (ascii):        VTT Temp Sensor

47.1.1.1.1.2.22 : OCTET STRING- (ascii):        VTT

47.1.1.1.1.2.23 : OCTET STRING- (ascii):        VTT Temp Sensor

47.1.1.1.1.2.1000 : OCTET STRING- (ascii):      WS-X6K-SUP1A-2GE 1000BaseX

Supervisor Rev. 3.1

47.1.1.1.1.2.1001 : OCTET STRING- (ascii):      Module Intake Temp Sensor

47.1.1.1.1.2.1002 : OCTET STRING- (ascii):      Module Exhaust Temp Sensor

47.1.1.1.1.2.1003 : OCTET STRING- (ascii):      Module  Device 1 Temp Sensor

47.1.1.1.1.2.1004 : OCTET STRING- (ascii):      Module  Device 2 Temp Sensor

47.1.1.1.1.2.1005 : OCTET STRING- (ascii):      L3 Switching Engine Container

47.1.1.1.1.2.1006 : OCTET STRING- (ascii):      L3 Switching Engine

47.1.1.1.1.2.1007 : OCTET STRING- (ascii):      L3 SE Intake Temp Sensor

47.1.1.1.1.2.1008 : OCTET STRING- (ascii):      L3 SE Exhaust Temp Sensor

47.1.1.1.1.2.1009 : OCTET STRING- (ascii):      L3 SE device1 Temp Sensor

47.1.1.1.1.2.1010 : OCTET STRING- (ascii):      L3 SE device2 Temp Sensor

47.1.1.1.1.2.1011 : OCTET STRING- (ascii):      CPU of supervisor

47.1.1.1.1.2.1012 : OCTET STRING- (ascii):      Ethernet Gigabit port interface

47.1.1.1.1.2.1013 : OCTET STRING- (ascii):      Ethernet Gigabit port interface

47.1.1.1.1.2.1014 : OCTET STRING- (ascii):      Container of Router Switch

Feature Card

47.1.1.1.1.2.2000 : OCTET STRING- (ascii):      WS-X6182-2PA FlexWAN Module Rev.

1.3

47.1.1.1.1.2.2001 : OCTET STRING- (ascii):      Module Intake Temp Sensor

47.1.1.1.1.2.2002 : OCTET STRING- (ascii):      Module Exhaust Temp Sensor

47.1.1.1.1.2.2003 : OCTET STRING- (ascii):      Module  Device 1 Temp Sensor

47.1.1.1.1.2.2004 : OCTET STRING- (ascii):      Module  Device 2 Temp Sensor

47.1.1.1.1.2.3000 : OCTET STRING- (ascii):      WS-X6248-RJ-45 10/100BaseTX

Ethernet Rev. 1.1

47.1.1.1.1.2.3001 : OCTET STRING- (ascii):      Module Intake Temp Sensor

47.1.1.1.1.2.3002 : OCTET STRING- (ascii):      Module Exhaust Temp Sensor

47.1.1.1.1.2.3003 : OCTET STRING- (ascii):      Module  Device 1 Temp Sensor

47.1.1.1.1.2.3004 : OCTET STRING- (ascii):      Module  Device 2 Temp Sensor

47.1.1.1.1.2.3005 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3006 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3007 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3008 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3009 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3010 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3011 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3012 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3013 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3014 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3015 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3016 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3017 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3018 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3019 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3020 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3021 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3022 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3023 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3024 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3025 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3026 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3027 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3028 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3029 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3030 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3031 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3032 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3033 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3034 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3035 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3036 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3037 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3038 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3039 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3040 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3041 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3042 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3043 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3044 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3045 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3046 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3047 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3048 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3049 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3050 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3051 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.3052 : OCTET STRING- (ascii):      10/100BaseTX

47.1.1.1.1.2.4000 : OCTET STRING- (ascii):      Router Switch feature Card

47.1.1.1.1.2.4001 : OCTET STRING- (ascii):      RSFC Intake Temp Sensor

47.1.1.1.1.2.4002 : OCTET STRING- (ascii):      RSFC Temp Sensor

47.1.1.1.1.2.4003 : OCTET STRING- (ascii):      RSFC device1 Temp Sensor

47.1.1.1.1.2.4004 : OCTET STRING- (ascii):      RSFC device2 Temp Sensor

47.1.1.1.1.2.4005 : OCTET STRING- (ascii):      Route Switch

47.1.1.1.1.2.5000 : OCTET STRING- (ascii):      WS-X6380-NAM Network Analysis

Module Rev. 1.1

47.1.1.1.1.2.5001 : OCTET STRING- (ascii):      Module Intake Temp Sensor

47.1.1.1.1.2.5002 : OCTET STRING- (ascii):      Module Exhaust Temp Sensor

47.1.1.1.1.2.5003 : OCTET STRING- (ascii):      Module  Device 1 Temp Sensor

47.1.1.1.1.2.5004 : OCTET STRING- (ascii):      Module  Device 2 Temp Sensor

47.1.1.1.1.2.5005 : OCTET STRING- (ascii):      Net Analysis

47.1.1.1.1.2.5006 : OCTET STRING- (ascii):      Net Analysis

#

الآن، لقد قمت بربط الفهارس بالوصف وربط الفهارس بقيم درجة الحرارة.

4. عمل الرابط بين قيم درجات الحرارة والوصف.

إستخراج هذه المعلومات من الخطوة 3:

47.1.1.1.1.2.1001 : OCTET STRING- (ascii):      Module Intake Temp Sensor

47.1.1.1.1.2.1002 : OCTET STRING- (ascii):      Module Exhaust Temp Sensor

47.1.1.1.1.2.1003 : OCTET STRING- (ascii):      Module  Device 1 Temp Sensor

47.1.1.1.1.2.1004 : OCTET STRING- (ascii):      Module  Device 2 Temp Sensor

واستخلاص هذه المعلومات من الخطوة 1:

9.9.91.1.1.1.1.4.1001 : INTEGER: 19

9.9.91.1.1.1.1.4.1002 : INTEGER: 28

9.9.91.1.1.1.1.4.1003 : INTEGER: 22

9.9.91.1.1.1.1.4.1004 : INTEGER: 28

النتيجة تعطيك:

- مستشعر درجة حرارة إدخال الوحدة النمطية = 19 درجة مئوية

- مستشعر درجة حرارة عادم الوحدة النمطية = 28c

- جهاز الوحدة النمطية 1 مستشعر درجة الحرارة = 22c

- جهاز الوحدة النمطية 2 مستشعر درجة الحرارة = 28c

نظرة عامة على OIDs في Cisco-entity-sensor-MIB

"org"                                   "1.3"

"dod"                                   "1.3.6"

"internet"                              "1.3.6.1"

"directory"                             "1.3.6.1.1"

"mgmt"                                  "1.3.6.1.2"

"experimental"                          "1.3.6.1.3"

"private"                               "1.3.6.1.4"

"enterprises"                           "1.3.6.1.4.1"

"cisco"                                 "1.3.6.1.4.1.9"

"ciscoMgmt"                             "1.3.6.1.4.1.9.9"

"entitySensorMIB"                       "1.3.6.1.4.1.9.9.91"

"entitySensorMIBObjects"                "1.3.6.1.4.1.9.9.91.1"

"entitySensorMIBNotificationPrefix"     "1.3.6.1.4.1.9.9.91.2"

"entitySensorMIBConformance"            "1.3.6.1.4.1.9.9.91.3"

"entSensorValues"                       "1.3.6.1.4.1.9.9.91.1.1"

"entSensorThresholds"                   "1.3.6.1.4.1.9.9.91.1.2"

"entSensorValueTable"                   "1.3.6.1.4.1.9.9.91.1.1.1"

"entSensorValueEntry"                   "1.3.6.1.4.1.9.9.91.1.1.1.1"

"entSensorType"                         "1.3.6.1.4.1.9.9.91.1.1.1.1.1"

"entSensorScale"                        "1.3.6.1.4.1.9.9.91.1.1.1.1.2"

"entSensorPrecision"                    "1.3.6.1.4.1.9.9.91.1.1.1.1.3"

"entSensorValue"                        "1.3.6.1.4.1.9.9.91.1.1.1.1.4"

"entSensorStatus"                       "1.3.6.1.4.1.9.9.91.1.1.1.1.5"

"entSensorValueTimeStamp"               "1.3.6.1.4.1.9.9.91.1.1.1.1.6"

"entSensorValueUpdateRate"              "1.3.6.1.4.1.9.9.91.1.1.1.1.7"

"entSensorThresholdTable"               "1.3.6.1.4.1.9.9.91.1.2.1"

"entSensorThresholdEntry"               "1.3.6.1.4.1.9.9.91.1.2.1.1"

"entSensorThresholdIndex"               "1.3.6.1.4.1.9.9.91.1.2.1.1.1"

"entSensorThresholdSeverity"            "1.3.6.1.4.1.9.9.91.1.2.1.1.2"

"entSensorThresholdRelation"            "1.3.6.1.4.1.9.9.91.1.2.1.1.3"

"entSensorThresholdValue"               "1.3.6.1.4.1.9.9.91.1.2.1.1.4"

"entSensorThresholdEvaluation"          "1.3.6.1.4.1.9.9.91.1.2.1.1.5"

"entSensorThresholdNotificationEnable"  "1.3.6.1.4.1.9.9.91.1.2.1.1.6"

"entitySensorMIBNotifications"          "1.3.6.1.4.1.9.9.91.2"

"entitySensorMIBCompliances"            "1.3.6.1.4.1.9.9.91.3.1"

"entitySensorMIBGroups"                 "1.3.6.1.4.1.9.9.91.3.2"

"entitySensorMIBComplianceV01"          "1.3.6.1.4.1.9.9.91.3.1.1"

"entitySensorValueGroup"                "1.3.6.1.4.1.9.9.91.3.2.1"

"entitySensorThresholdGroup"            "1.3.6.1.4.1.9.9.91.3.2.2"

نظرة عامة على OIDs في ENTITY-MIB

"org"                                   "1.3"

"dod"                                   "1.3.6"

"internet"                              "1.3.6.1"

"directory"                             "1.3.6.1.1"

"mgmt"                                  "1.3.6.1.2"

"experimental"                          "1.3.6.1.4.1"

"private"                               "1.3.6.1.4"

"enterprises"                           "1.3.6.1.4.1"

"mib-2"                                 "1.3.6.1.2.1"

"entityMIB"                             "1.3.6.1.2.1.47"

"entityMIBObjects"                      "1.3.6.1.2.1.47.1"

"entityMIBTraps"                        "1.3.6.1.2.1.47.2"

"entityConformance"                     "1.3.6.1.2.1.47.3"

"entityPhysical"                        "1.3.6.1.2.1.47.1.1"

"entityLogical"                         "1.3.6.1.2.1.47.1.2"

"entityMapping"                         "1.3.6.1.2.1.47.1.3"

"entityGeneral"                         "1.3.6.1.2.1.47.1.4"

"entPhysicalTable"                      "1.3.6.1.2.1.47.1.1.1"

"entPhysicalEntry"                      "1.3.6.1.2.1.47.1.1.1.1"

"entPhysicalIndex"                      "1.3.6.1.2.1.47.1.1.1.1.1"

"entPhysicalDescr"                      "1.3.6.1.2.1.47.1.1.1.1.2"

"entPhysicalVendorType"                 "1.3.6.1.2.1.47.1.1.1.1.3"

"entPhysicalContainedIn"                "1.3.6.1.2.1.47.1.1.1.1.4"

"entPhysicalClass"                      "1.3.6.1.2.1.47.1.1.1.1.5"

"entPhysicalParentRelPos"               "1.3.6.1.2.1.47.1.1.1.1.6"

"entPhysicalName"                       "1.3.6.1.2.1.47.1.1.1.1.7"

"entPhysicalHardwareRev"                "1.3.6.1.2.1.47.1.1.1.1.8"

"entPhysicalFirmwareRev"                "1.3.6.1.2.1.47.1.1.1.1.9"

"entPhysicalSoftwareRev"                "1.3.6.1.2.1.47.1.1.1.1.10"

"entPhysicalSerialNum"                  "1.3.6.1.2.1.47.1.1.1.1.11"

"entPhysicalMfgName"                    "1.3.6.1.2.1.47.1.1.1.1.12"

"entPhysicalModelName"                  "1.3.6.1.2.1.47.1.1.1.1.13"

"entPhysicalAlias"                      "1.3.6.1.2.1.47.1.1.1.1.14"

"entPhysicalAssetID"                    "1.3.6.1.2.1.47.1.1.1.1.15"

"entPhysicalIsFRU"                      "1.3.6.1.2.1.47.1.1.1.1.16"

"entLogicalTable"                       "1.3.6.1.2.1.47.1.2.1"

"entLogicalEntry"                       "1.3.6.1.2.1.47.1.2.1.1"

"entLogicalIndex"                       "1.3.6.1.2.1.47.1.2.1.1.1"

"entLogicalDescr"                       "1.3.6.1.2.1.47.1.2.1.1.2"

"entLogicalType"                        "1.3.6.1.2.1.47.1.2.1.1.3"

"entLogicalCommunity"                   "1.3.6.1.2.1.47.1.2.1.1.4"

"entLogicalTAddress"                    "1.3.6.1.2.1.47.1.2.1.1.5"

"entLogicalTDomain"                     "1.3.6.1.2.1.47.1.2.1.1.6"

"entLogicalContextEngineID"             "1.3.6.1.2.1.47.1.2.1.1.7"

"entLogicalContextName"                 "1.3.6.1.2.1.47.1.2.1.1.8"

"entLPMappingTable"                     "1.3.6.1.2.1.47.1.3.1"

"entAliasMappingTable"                  "1.3.6.1.2.1.47.1.3.2"

"entPhysicalContainsTable"              "1.3.6.1.2.1.47.1.3.3"

"entLPMappingEntry"                     "1.3.6.1.2.1.47.1.3.1.1"

"entLPPhysicalIndex"                    "1.3.6.1.2.1.47.1.3.1.1.1"

"entAliasMappingEntry"                  "1.3.6.1.2.1.47.1.3.2.1"

"entAliasLogicalIndexOrZero"            "1.3.6.1.2.1.47.1.3.2.1.1"

"entAliasMappingIdentifier"             "1.3.6.1.2.1.47.1.3.2.1.2"

"entPhysicalContainsEntry"              "1.3.6.1.2.1.47.1.3.3.1"

"entPhysicalChildIndex"                 "1.3.6.1.2.1.47.1.3.3.1.1"

"entLastChangeTime"                     "1.3.6.1.2.1.47.1.4.1"

"entityMIBTrapPrefix"                   "1.3.6.1.2.1.47.2"

"entityCompliances"                     "1.3.6.1.2.1.47.3.1"

"entityGroups"                          "1.3.6.1.2.1.47.3.2"

"entityCompliance"                      "1.3.6.1.2.1.47.3.1.1"

"entity2Compliance"                     "1.3.6.1.2.1.47.3.1.2"

"entityPhysicalGroup"                   "1.3.6.1.2.1.47.3.2.1"

"entityLogicalGroup"                    "1.3.6.1.2.1.47.3.2.2"

"entityMappingGroup"                    "1.3.6.1.2.1.47.3.2.3"

"entityGeneralGroup"                    "1.3.6.1.2.1.47.3.2.4"

"entityPhysical2Group"                  "1.3.6.1.2.1.47.3.2.6"

"entityLogical2Group"                   "1.3.6.1.2.1.47.3.2.7"

"entityNotificationsGroup"              "1.3.6.1.2.1.47.3.2.5"

إخراج الأمر show environment temperature من خلال CLI

ملاحظة: يجب أن تكون في وضع التمكين لإصدار الأمر show environment temperature.

zatar> (enable)#show environment temperature

Intake        Exhaust       Device 1     Device 2

Slot             Temperature   Temperature   Temperature   Temperature

---------------  ------------  ------------  ------------  ------------

1                19C(50C,65C)  28C(60C,75C)  21C           27C

2                20C(50C,65C)  20C(60C,75C)  N/A           N/A

3                16C(50C,65C)  25C(60C,75C)  26C(70C,85C)  N/A

4                17C(50C,65C)  20C(60C,75C)  19C           24C

1  (Switch-Eng)  19C(50C,65C)  23C(60C,75C)  N/A           N/A

1  (MSFC)        24C(50C,65C)  29C(60C,75C)  N/A           N/A

Chassis Modules

------------------

VTT1: 20C(85C,100C)

VTT2: 21C(85C,100C)

VTT3: 19C(85C,100C)

zatar> (enable)

استكشاف الأخطاء وإصلاحها

يرسل المحول CiscoEnvMonTemperatureStatusDescr=module[no]

يرسل المحول رسالة SNMP CiscoEnvMonTemperatureStatusDescr=Module [no] كإعلام بأن درجة الحرارة التي يتم قياسها عند نقطة إختبار معينة تقع خارج النطاق الطبيعي لنقطة الاختبار. يمكن أن يكون النطاق في إحدى هذه المراحل:

- تحذير

- حرج

- الإغلاق

يحدد خيار نطاق الحالة الحالية في مصيدة إعلام SNMP أي من هذه النطاقات الثلاثة لدرجة الحرارة تقع الوحدة النمطية. يحدد خيار مدة الفحص في مصيدة إعلام SNMP المدة الزمنية التي تكون فيها درجة حرارة المحول أعلى من النطاق العادي.

إذا كانت الحالة الحالية لدرجة الحرارة في نقطة الاختبار للوحدة النمطية في مرحلة إيقاف التشغيل، يقوم المحول بإيقاف تشغيل الوحدة النمطية تلقائيا. رسائل CiscoEnvMonTemperatureStatusDescr = module[no] هي رسائل إعلامية.

الحل المقترح لتجنب المشاكل غير المتوقعة هو ضمان الحفاظ على درجة الحرارة حول المحول في حدود معايير التشغيل التي تحددها مواصفات الوحدة النمطية. رأيت الإنتاج من العرض بيئة درجة حرارة أمر من خلال ال CLI قسم من هذا وثيقة in order to جعلت هذا درجة حرارة تحديد. أيضا، تأكد من أن المراوح الداخلية في المحول تعمل بشكل طبيعي.

معلومات ذات صلة

- الملاحظات الفنية لتصميم خدمات تطبيق IP

- مراقبة البيئة إدارة المحول

- الدعم التقني والمستندات - Cisco Systems